My situation was effectively analyzed and addressed in an effective manner. I was pleased with the result.
Jim with Bradbury Brothers was extremely knowledgable and so very easy to talk with. A true professional.
I'm not disappointed in Ernest, but I am disappointed that the unit is not performing as intended. I spent over $15,000 on this unit and I was told that it would be sufficient for my building. The unit cannot keep the temp below about 78 or 80 degrees during the afternoon. Ernest told me that someone would contact me and I haven't been contacted.
I would recommend this company to others.
I'm very pleased with the job that Jim performed in making the electrical connection to the new HVAC unit that was installed by Bradbury Brothers. Jim was very prompt at arriving at the time agreed upon and did a very nice job. Thank you
Henry was courteous, and explained about the features in my system he checked.
Response from Bradbury Brothers Cooling, Plumbing & Electrical:
Thank you for the 5 stars, Lee!
AC Diagnostic System:main Control for surge protector are no longer functional, will need to have surge protector replaced tomorrow. Bypassed the surge protector to get the unit operational tonight . Nobody will be home to replace the surge protector, so if we are needing to drop the temperature for any reason Sam asks that we call him so he can control it by phone.
Customer had us out today for a slow draining sink in the master bath. Ran hand top to clear blockage. Filled and drained the sink multiple times to test for leaks and functionality, everything is operating as it should. No warranty on drain cleaning.
System-main Approx Age of System: 8 Refrigerant Type- R410a Metering Device- TXV SP/HP:118/298 SLT/LLT:62/94 VSAT/LSAT- 46/102 Superheat/Subcool-16/7.6 Outdoor Entering Air Temp-78 Outdoor Fan FLA- 1.1 Compressor RLA/LRA-12.1/74 Contactor Voltage-28/220 Indoor Return Dry Bulb Temp-74 Supply Temp-56 Temperature Difference-18 Required Difference-16-22 Blower FLA- 3.2 Filter Sizes â€“ 20x25x1 Changed Filters â€“ Y (customer provided) Blew out drain line: N no blow out valve Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes-System is fully operational, filter was dirty and replaced. No other issues were visible, Scheduled next tune up date:Jan 21st 8-10
Diagnostic Found 55/5uf run cap failed. Replaced with Turbo 200. System function restored. 90/292 psi 58/112 lt 52/130 sat 4/16 shsc Condenser coil is starting to deteriorate. System is running very hot. Compressor is struggling audibly at start up. System utilizes r22. Based on age, conditions and operational concerns - system replacement is recommended. Trust owned home.
We came out today to conduct the annual plumbing home inspection. We ended up giving an estimate to replace the cartridge in the upstairs guest bathroom tub, replace the angle stops and supply lines in that same bathroom sink because they were polybutylene and most likely will one day be a serious issue, and to replace the supply line on the Toilet in that bathroom because itâ€™s a problematic product and not recommended. Also gave an estimate to the customer to replace the water heater because they know it is all then near the end of its life expectancy but assured them we will be replacing it with the same quality rheem Product. Other than that the house looks great no serious issues to bring up to the customer and they will call us when theyâ€™re ready to make these repairs.
Came out today to give the customer pricing on changing out the water heater in the garage. Customer okayed the estimate and we went ahead with the work. The customer now has a new 40 gallon electric water heater installed with a pan. Customer paid with credit card no follow-up needed today.
System- Main Approx Age of System: 5yrs Refrigerant Type- R410a Metering Device- Fixed Orifice SP/HP: 122/303 SLT/LLT: 59/86 VSAT/LSAT- 41/96 Superheat/Subcool- 17/10 Outdoor Entering Air Temp- 82 Outdoor Fan FLA- 1.2 Compressor RLA/LRA- 10.3/117 Contactor Voltage-242/26 Capacitor Rating- 68.01/14.75 Indoor Return Dry Bulb Temp-75 Return Wet Bulb Temp- 59 Supply Temp- 55 Temperature Difference- 20 Required Difference- 16-20 Filter Sizes â€“ 20x30x1 Changed Filters â€“ Acceptable Blew out drain line: Y Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes- Unit was operational on arrival. Checked filters. Checked operating pressures and temperatures. Checked indoor and outdoor electrical. Condenser LRA is over rating of 117a. All other components showed no visible issues at this time. Recommend compressor saver-(to reduce amp and extend equipment life). Installed compressor saver. Checked operation. Scheduled next tune up date
AC Diagnostic System:main Refrigerant Type R410A Metering Device-TXV SP/HP105.5/342.7 SLT/LLT74.5/96.4 VSAT/LSAT34.4/105.1 SH/SC40/8.7 Outdoor Entering Air Temperature 90 Filter Size(s)20x25x4(Lennox media filter) Returned tstat to original settings: Y(did not touch) Unit operational; prior to leaving: Y Notes:Upon arrival, Mr.Cotton explained that we had been out last month and cleared the drain line but when he went up to the attic recently he saw there was water in the drain pan. The unit is upflow and the secondary drain port to the coil was capped off so water was overflowing in the primary drain line going through the blower and existing out of the seams of the bottom of the furnace. Homeowner authorized fixing drain line to have secondary port drain into the emergency drain pan. Explained that there was a large amount of rust on the coil and there is a high chance of primary drain line getting clogged again. When recording unit pressures, found the suction pressure low for
Arrived to the Rector residence to go over generator ideas. Got information for Todd and Ron that way we can put a price together. At this time thereâ€™s no reason to do a follow up call.
Customer had us out today for a leak on the main line. Found the 90 going towards the house leaking. Made the repair, allowed glue to cure for 20 minutes and turned water back on. No signs of leaking and everything seems to be working as it should.
AC Diagnostic System: Refrigerant Type R410A Metering Device- TXV SP/HP 141/375 SLT/LLT 61/98 VSAT/LSAT 49/111 SH/SC 11/13 Outdoor Entering Air Temperature 90 Filter Size(s) 20x25x1 Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes: Unit is operational on arrival. Checked safety switches. Water is present in emergency drain pan. Checked operating temperatures and pressures. Head pressure is a little high. No issue. Primary drain line is clogged/restricted. Cleared drain line and checked for flow. Recommendations: Drain line flush, condenser coil clean
Master shower as constantly running. Shower cartridge wS bad and needed to be replaced . Turned water off and installed new moen cartridge and tested for leaks. Found none
Run capacitor failure. Replaced with Turbo 200, system function restored. System is over amping on startup despite having a functional hardstart. R22 system. Filter dryer is rusting out. Condenser coil is deteriorating. Replacement is strongly recommended. RP- .12 /FR- .38 /FS- .29 /SP- .1 TESP: .67 Skylar scheduled 07/03 5-6
Free water test and filter install estimates. Customer has bought her own aquasona system and would like us to install it. Estimates provided and will be installed Wednesday