George exaplimed everything in layman’s terms and was extremely knowledgeable and friendly.
Budget always does a great job. Their Techs are top notch and always do a outstanding job
Greg was everything you could ask for from a plumber. He is highly competent, diligent, meticulous, customer focused and forward thinking in communicating ways to prevent issues from happening in the future. If I owned a plumbing company, Greg would be my first pick in the draft.
Quick and easy clean/maintenance
Beau was great. He didn’t just come in and not say a word he was very nice and also explained what he was doing and sometimes what the causes were when your heater stops working. Also found the safety bar and reattached it. He was Great
Our plumber George was prompt, courteous and very knowledgeable. We had an unusual leak from our washing machine drain that he quickly analyzed and came up with a creative repair that worked well. Very satisfied with his service and competence.
Greg is a true problem solver and is very nice and professional
Highly recommend, the technician was very thoughtful and honest about what was going on.
Furnace repair. Lennox. Replaced gas valve on furnace
Repaired hot water heater
Gas Piping Upon arrival the customer stated that the gas company had found leaks in the gas line and shut the gas off to home. Started with checking the main gas line going from outside to the furnace and water heater. The gas lines split up right inside the basement and It has 2 runs of pipe. One went to the furnace only and one going to water heater, then on through the house to the laundry room. I disconnected the line going to laundry room and started there going back to the outside. Got a leak in my 1st pressure test at a 1/2” tee. Removed that from run and tested again the 2 main lines. Held pressure on the 1st test, held on the 2nd test. Tested once more to be sure and it’s good. Now I got setup on the line going to dryer and another line in the laundry room. 1st test, I had a leak, but it was a small one. Resprayed leak detector on fitting and tested again. Still wasn’t showing any bubbles but was leaking somewhere. Since there was this extra gas line in laundry room, I removed
Carrier packaged unit. Replaced draft inducer motor and wheel
Plumber, plumbing, faucet repair, leak repair. Repaired leaking faucet
HVAC technician, heating, Furnace repair. Heil. Replaced control board and cleaned out pilot orifice
HVAC technician, heating, furnace repair. O'fallon, MO. Cleaned furnace out. Pulled and cleaned all burners. Found one burner was bent out.Was able to repair. Cleaned flame sensing rod. Checked all safetys. Test fired system all kicked in. System is heating.
HVAC technician, heating, Furnace repair. Carrier. Replaced ICM281 control board on furnace.
HVAC technician, heating, furnace repair. No heat. Found inducer and 5mfd bad. Able to free up inducer. Replaced 5mfd. System heating well. Customer doesn’t wanna replace inducer yet
Plumber, plumbing, garbage disposal installation, garbage disposal replacement. Installed new garbage disposal
Air handler repair. Lennox. Found thermostat set for gas heat instead of electric
Water Heater One Time Cleaning I did a cleaning of the burner assembly, chamber, fire screen and heat diverted plate. Once I got it cleaned up, put burner assembly back in, lit pilot, waited 25seconds, turned gas valve to the 120dergee setting, then waited to make sure that the high limit didn’t trip. Water heater heated up til it was satisfied and high limit didn’t trip. Should be OK now.
Furnace clean and check
Repaired instant hot water