Performed a three system maintenance, checked all electrical, mechanical and safety components, checked systems operations, changed filters, checked belts, cleaned condenser coils, all systems are operating properly at this time.
Upon arrival manager had stated that the unit was dripping water out of return but hasnâ€™t leaked since Saturday 10/23/21. Checked RTU2 and found that the p-trap was clogged up with debris, cleared out trap and inspected drain pan, found that there was debris built up on the bottom of the drain pan causing pan to have a lower flood rim, with approval cleaned debris out of pan, and placed pan tablets in pan to keep pan clean. System is now draining properly at this time.
Performed a 3 system maintenance checking cooling. Checked all electrical and mechanical components, checked drains, changed filters all components checked out good. Found that on RTU2 both condenser fan motors were shorted to ground. Emailed estimate over to replace both fan motors. Also replaced customer supplied belt on RTU 2.Quote#774523 at carrier.
Found condensate drain trap clogged. Cleared out trap. Emptied primary condensate pan. Poured water into pan and checked for proper drainage. Unit is draining properly at this time. Insulation in return is still wet and may drip a little longer but will stop once Insulation dries. Took temp reading on supply and return air. Checked refrigerant charge on both circuits. Unit is working properly at this time.
Complete installation of a Lennox hvac system.
New system install! Looks fantastic! 16 seer, after completing a manual J heat load calculation that measures the exact size system needed for the home based on windows, doors, insulation, and even the direction the home faces.
Air Conditioning repair and replacement made on 11 year old Trane 3 ton unit.