Upon arrival RTU2 was throwing an alarm for the duct detector. Checked RTU2 and found that the supply air detector was setting alarm off. Checked duct detector and found it dusty, cleaned off and blew out duct detector, put duct detector back together and turned system back on. Duct detector stopped tripping alarm. Tested heating and cooling. Got all equipment information and filter sizes. List of filters uploaded in pictures.
Lite water heater and capped off water lines to sink in garage. Customer does not want to put sink back. 03/05 Demoed right garage wall. Per Michael. Picture attached