Homeowner said unit seems to be struggling keeping up. Checked refrigerant charge. System is low on 410a. Recommended performing a leak search. Customer approved leak search. Found evaporator coil leaking and can't brazed leaks. Need to replace evaporator coil. Evaporator coil is under a parts warranty until 11/23. Found a bad 45/5 mfd run capacitor. Cleaned condensing coil and replaced capacitor. Blower motor was set too high. Changed blower speed to medium high. Customer wanted to charge unit up for the time being. Charged unit with 3 lbs of 410a. Ran system through cooling cycle took temp reading on supply and return air, checked static pressure on duct system. Static is a little high. Ductwork is undersized for system. Unit is cooling at this time. Will check availability and get back with Homeowner to schedule.