Upon arrival found system coming on but not cooling, checked outdoor unit and found the fan running but compressor not. Checked capacitor and found it not giving a reading on the compressor side. Lee had supplied the capacitor, changed capacitor and compressor came on. Checked amps on compressor and it was pulling 10.2/20.8. Checked Freon levels and they were good. System is now cooling properly at this time.