John did a great job
Great job. Very professional
Upfront explanations and professional workmanship (on time, courteous, clean, all of those!) and a fair price mean a quality job well done! Thank you again!
John was very pleasant and professional. He has serviced our home before and did an excellent job just as he did previously. We’d love having him service our home regularly, going forward.
The technician was knowledgeable, friendly and provided good feedback. Recommend them to everyone
John is a fine young professional who explains things thoroughly and honestly. Very trustworthy and dependable!
John is courteous and a nice guy.
Completed 5 unit commercial matience. All units are 1 year old and are still in good condition. I changed all filters, checked operation of heating and cooling on all units. Also checked amperages, capacitors and blew drain lines. All units are operating properly and safe to operate.
System is still purging in middle of the night. I checked all the pressures and everything looks normal. I changed some settings in the thermostat hoping it will stop the heat pump running so much and kick on electric heat sooner. Also thinking this could do with the TXV we replaced last summer (could need to be changed to a orphis). Customer is going to wait and see if the problem improves.
Found ignitor that had been replaced with board had failed, I replaced ignitor under warranty and unit is working properly.
Dispatched to water heater not working. Upon arrival water heater was functioning properly. Customer said that last night it was making a loud humming type of sound and the house had no hot water. I checked elements voltages of water heater and it seems to be working just fine at this time. Cuatomer was advised to keep an eye on it.
Completed inspection of damage problems. Aaron is going to make a quote to fix drains and replace three faucets.
Completed two system tune up. Today included a downstairs system furnace tune up. I also preformed a complementary upstairs tune up as well for the miscommunication on failed inspection reports. Both up and downstairs condenser fuses need to be changed in order to pass inspection with the city of Frisco. New 50 amp fuse box and 25 amp fuses (upstairs furnace) needs to be replaced. Office will call and schedule work to be done. Filter size for downstairs system is 20x24x4 01/13 Conpleted installation of new disconnect boxes in order for units to ass inspection. Pictires attached.
Performed tune up of heating system, also Performed plumbing inspection and looked at pedestal sink that customer would like to switch over to vanity. Will get with Aaron on specifics. All is working normally at this time.
Completed 2 system fall matience on downstairs trane and upstairs lennox systems. I checked operation, cleanliness, safety ect of unit and they are both operating correctly at this time. This is last matience under new system. So both memberships need to be renewed. UV light bulb is also out in main unit and needs to be replaced. Estimate attached. After talking to customer he showed me he has a 10 year matience with pleasant valley for main trane unit.
Completed two system matience on 18 year old furnaces. Both furnaces are showing there age has several parts are showing signs of failure. Blower motors are leaking oil, inducer draft motors are over Ampang, boards have burn marks on back of them. Customer was advised to start thinking about system replacement in lieu of the coming repairs.
Repair tub drains on 2 upstairs showers. Remove and replace sheetrock. Texture and paint access area.
Completed one system fall matience. Unit is 1 year old and is heating properly at this time. Safety switches were also functioning properly as well. Filter was changed.
Recommendation for continued heat. Current heat kit is completely rusted out and could be causing problems in heating elements. Replacement of heat kit is recommended.
Completed system replacement estimate
Completed installation of M30 thermostat. Tested both heating and cooling of system before I left. Replace upstairs thermostat with M-30 thermostat
Installed new humidistat as well as outdoor temperature sensor. Also programed humidistat to run on automatic using the odts. Programmed at 55% humidity.