Check amp draws, check Freon levels, check Contactors , check filters, 1st floor unit was low on Freon, found that the valve stems had slow leaks on them. Noticed that there was oil all over one of the caps. Maintenance approved replacement of valve stems. Replaced valve stems and charged unit back up with customer supplied 407c. 3rd floor unit had the bad compressor. All other systems checked out good.