Performed maintenance on 4/5 units. Unit number three still has the bad compressor, checked filters, amp draws, capacitors, contactors, pressures, all systems checked out good. Checked temperature differential. Unit 6 does need a filter change out and maintenance said theyâ€™ll have some for the next visit. Systems are cooling properly at this time.