Timely. Good job
Professional and thorough
Initial visit. Great first impression. Very Professional
After much confusion we got where we needed to be. Thanks for all your help
Ray was the technician who arrived at my home. He was professional, knowledgeable and polite. He diagnosed two separate issues with my A/C unit. He successfully negotiated with Choice Home Warrenty on both issues and made the repairs in a timely manner. I was very impressed with his competency and the ease inwhich he made the repairs. He provided me with many of the services your company offers as well. If Ray is an example of the caliber of all your employees I will certainly call your company in the future!! One more thing the woman who handles all your calls is also fantastic. She was very helpful in assisting me make my appointment. Her demeanor was friendly, efficient and professional. She was the first person from your company who left me with a great impression!!!
Dispatched to unit making noise. After diagnostic I found that the compressor was bad. After changing the compressor and charging the unot appropriately the unit is cooling.
Call back to same dirty sick syndrome. Coil is 2 years old ADP. UV light was installed in November but smell still persists. I have now opened coil box completely and cleaned coil. We will see if the cleaning will solve our problem.
Preformed one system fall matience on new lennox furnace. Blower motor amps 12.8 max/ 6.1 acutal, inducer draft motor .26 amps, capacitor 5/4.98. Also checked furnace safety switches and unit is operating properly at this time. April air 210 will b ready to change during spring matience
Dispatched to unit smelling when air conditioning comes on after being off. I checked the cleanliness of the coil and the coil was spotless. To resolve issue I installed a 4 inch filter instead of 1 inch and unstalled UV light to keep coil free of bacterial growth and help with smell. Install UV light for whole home air purification, with ozone to help get rid of sock smell.
Completed 3 system fall matience. Also cleaned clogged sink "on the house" as a thanks for being our customer. Also took concrete pad from side of house and set up his thermostats.
Completed one system estimate for replacing upstairs three ton unit. See options for details. Nathan (469) 678-1194
Performed plumbing inspection, removed master bath airiators in sinks. Inspected rinnai
Completed one system tune up. System is operating properly at this time. Blower :5.6A Compressor S:97 Compressor R: 13.7 Condenser fan: 0.97 Pressures:138/342
Upon arrival house wasn't cooling. Thermostat was satisfied at 74 degrees when it was 82 inside the home. I took the thermostat off the wall and reset the m30. After it rebooted the system corrected itself and is working properly at this time.
Air conditioner not cooling monitor air conditioning and heat pump systems for correct refrigerant charge.
Giving a written quote on customers 2nd unit. Replaced 1 system already.
Preformed a summer maintenance on the system, checked the inside and outside unit. Still looked great install was only year old
Inspection of customers furnace and possible complete system, . Inspected the complete system and gave customer a quote on a new 4 ton Lennox two speed and single speed, 16 seer system after completing a manual J heat load calculation that measures the exact size system needed for the home based on windows, doors, insulation, and even the direction the home faces.
Summer maintenance on a Lennox hvac system.