John came in to inspect my system. He was professional and polite. He left my come clean and provided excellent customer service. I highly recommend him for all your HVAC needs
Very professional and did a great job.
From scheduling to the actual completion of the service, everything went smoothly. Service tech was very professional and courteous and was able to answer all questions. He performed the service in a timely manner and made adequate recommendations. Can definitely recommend this company's services.
After signing up for the service plan they have been on time and here twice a year. George was great and professional. Went over everything he did before he left.
Jorge was a pro tech and super nice. Fast and efficient and was in and out quick. Thanks for the service Sir. You will be my go to tech from here on out. Happy Fathers Day!
Amazing experience. The staff was knowledgeable, professional and prompt!
Unit was low on refrigerant but been having issues since we installed it system needs to be leak checked.
Found fire suppression system among other things, damage is unknown at this time. We will need to return and further assess.
Dispatched to no heat. Previous company diagnosed as faulty inducer motor and was going to charge 1400 to replace. I arrived to the same diagnostic and replaced inducer motor. Both upstairs and downstairs are heating properly upon departure. Pictures attached
Completed one system estimate. Estimates attached
Completed one system home inspection on 13 year old carrier heat pump/ air handler. Heat is running in 2nd stage only (heat strips) and is pulling a 69/99 delta T. Heating 1st stage isn't running as well as the A/c. After further inspection the heat pump has 0/0 R2w refrigerant left in the system. Couldn't do whole inspection due to system not running. Owner was advised that replacement was best option.
Customer had some concerns about dust and debris in his outdoor units due to construction of the home next door. There is dust in the bottom of unit that will not do any harm to unit. I was able to free some grout from the too of the fan blades. Units are in great shape.
Checked ac coil, inspected blower and compartment. Found no signs of oil, also ran heat for extended period of time. No oil smell was detected but customer will continue to observe.
Called for fall tune up. After testing system condenser wasn't working outside. After diagnostic the compressor has failed and was throwing the breaker. Gave options on compressor changeout, new condenser, and conplete systems. Estimates attached.
Advised on how to do HVAC service repairs.
Completed one system fall heating maintenance on 5 month old heat pump. HVAC system unit is operating and heating correctly at this time.
Completed one system heat check. Everything operating properly at this time. Customer would like us to bring filter (Y6604) for next visit and would like us to bring one on every other visit (once a year) System just installed this year. No options given.
Took photos and videos of 2 ac indoor coils. Found appearant refrigerant leaks on each coil. Coils also show heavy rust throughout.
One system diagnostic. System is empty of R22 Refrigerant. See all options for details.
Customer has had several companies out to work on system. Unable to diagnose system at this time because of improper wiring safety hazard. Gave options on proper wiring and replaceing defrost board
Provided one system estimate. See options for details. No email on file. Customer wrote everything down.