Performed a two system maintenance checking cooling. Checked inside units electrical and mechanical components. Found that both blower capacitors were weak. Then checked outdoor units pressures amp draws and capacitors. Found that the downstairs unit is pulling high amps on compressor and fan motor. Compressor and fan motor could fail soon. Recommended start assist for downstairs condenser. Gave other recommendations and homeowner wanted to hold off on repairs.