Jeremy always dos a good job
Jeremy was excellent checked everything made suggestions not pushy well done
Jeremy came out and was professional from the start!! He kept coverings for his shoes to respect our carpet, took the time to diagnose the problem and even went above and beyond to make sure there wasn’t anything he could do to save the thermostat and parts. He explained the diagnosis and helped set things in motion to fix the issue. Great call back time and customer service!! I can see why this company has such high ratings!!
Had a great experience! Super helpful!
Josh provide info on the system as he was checking the heating system.
Representative was clean and friendly, feet covered in and out in about 30 min.
Very thorough and appreciate johns suggestions
Our A/C started warming up, They were here in about two hours, we have used CHROME in the past and were glad that they sent someone we had seen before
30 minutes after i called Nathan was at my dooe
Upon arrival found that there are three units not cooling, there’s two big split units on the third floor that do the hallways and on package units that does the left side of the lobby. On the package unit I found that it was empty on refrigerant, found a bad belt and a cracked heat exchanger, with systems age and condition recommended replacement. Was unable to get all the tag information on package unit due to placement and a duct run. For the hallways on left side found system empty on refrigerant and one of the condenser fan motors spinning backwards. On the right side for hallways found that system empty on refrigerant as well as a bunch of wires disconnected with no schematic to figure out where wires go. Due to refrigerant, age and condition system will have to be replaced. Uploaded all information and pictures of where units are located, will need a crane for package unit and the condenser for left side due to it being on roof, roof height is around 25-30feet and about 50-60 fe
Springtime Air Conditioning Repair for a residential customer near Deerfield. Came out today for service call on right side of house r22 2005 unit. Found Dirty 20/20/1 filter. Bad 7.5 run capacitor for blower motor. Insulation levels are low costing more electricity and making units run/work harder. (Disconnect was not fully in pushed in. 240 coming in 50 coming out. [Pushed plug all the way back in.] Now 240 coming in 240 coming to condenser.) Turned on thermostat Checked bearings checked blades checked electrical connections checked contactors checked run capacitors checked Amp draws checked pressures checked filter checked temp split checked duct work checked insulation levels.
Springtime Air Conditioning Repair for a commercial client near Wooded Creek. Upon arrival customer States that only the lobby unit wasn’t cooling. Checked outdoor unit and found the system low on charge and condenser coil completely clogged. Checked indoor units evaporator coil and found oil on suction line. Traced it back to the pressure port for the txv. Was able to tighten port half a turn. Checked coil with leak detector and picked up nothing. With approval washed coil and added 7lbs of 410-A to set charge. System is now cooling properly at this time.
Springtime Thermostat Replacement for a residential customer near Northridge Estates. Came out on service call in Plano with a blank thermostat. Icomfort thermostat is white screened and wants to Replace thermostat with icomfort s30 and customer wants quote replacement tstat.
Came out today on a 3 system maintenance Checked pressures checked duct work checked insulation levels cleared drains cleaned outdoor coils changed 2 or 3 units filters checked Amp draws checked bearings checked blades checked contactors checked run capacitors checked electrical connections Found 2ton Unit in garage attic 2b2g: Bad 7.5 run cap Dirty filter needs to be changed 20x25x1 Dirty duct work Dirty blower wheel 2 square boxes 5ton unit furthest in attic upstairs 861G: Bad 15 run cap Dirty blower wheel Dirty duct work Cracked/rusted secondary drain pan Main return to unit hanging not attached so unit sucking in attic air. 3.5ton small unit in upstairs attic s92g: Main return to unit not fully attached and hanging so unit is sucking in attic air Dirty duct work Bad 5 run cap 12seer r22 2ton condenser fd2f: Low on r22 High Amp draw on condenser fan motor meaning possible part failure Dirty condenser coil / cleaned. 3.5 410a condenser 273f: Bad 7.5 run cap Contactor is burnt
Emergency HVAC Repair Service near Preston Bend. Upon arrival found system not cooling. Checked indoor unit and found 19 year old evaporator rusting pretty bad. System came on and operating pressures inside. Checked outdoor unit and found system low on refrigerant. Added 3 pound to system to set charge. Refrigerant does have the potential to leak back out. System is now cooling at this time.
Upon arrival turned system on and could hear compressor making a loud grinding noise, hooked up gauges and system was not moving refrigerant. Scrolls inside compressor had busted and compressor would have to be replaced. System has a txv and with scrolls busted fragments may have been sent up to the txv, txv will need to be changed out as well. Parts ordered from Lennox in Allen, compressor will be at the Allen store in the morning. Parts and labor are covered under warranty. Upon arrival removed all refrigerant from system, cut out old filter dryer and brazed out old compressor. Installed new filter dryer and compressor while purging with nitrogen. Unbolted old txv And installed new txv. Pressure tested system at 175psi and pressures held. Released nitrogen and pulled vacuum down to 500 microns. Added a total of 8.5lbs to set charge. Checked static pressures and lowered blower speed down to medium high. Checked amp draws. System is now operating properly at this time. Compressor was
Provided an estimate for a residential customer near Windhaven Farms. Gave estimates for three systems, ductwork is older but in good shape, I didn’t find any signs of Deterioration however ductwork would need to be strapped back up in some locations to improve airflow, systems are two four tons and one two ton. All systems would need new supply and return plenums. Gave estimates for a 14, 16, and 18 seer. Homeowner wanted estimates emailed to him.
Springtime Emergency Air Conditioning Repair for a residential customer near Family Farm. Came out on water leak service call Water dripping from staircase to attic from a secondary drain pan that was full and was dripping over the corner Both units in attic are tied together. Installed shutoff to one side of drain line and coupling on other drain line after cleared and double checked drain line was clear put lines back together. Found cracked upstairs secondary pan meaning if it gets water in that pan will have another water leak. Cleared secondary drain line from pan to allow water to leave secondary pan properly.
Springtime Air Conditioning Maintenance for a residential customer near Preston Village. Came out on 1 system maintenance Checked temp split checked bearings checked blades checked filter checked amp draws checked electrical connections checked duct work checked pressures checked run capacitors checked contactors checked coils checked drain line Found 1 inch filter getting dirty Customer states will replace it soon. No surge protection No IAQ (air purifier)
Springtime Air Conditioning Maintenance for a residential customer near Laurel Lane. Upon arrival performed a one system maintenance checking cooling. Starting with indoor unit, checked all electrical, mechanical and safety components, checked filter and amp draws and static pressures. Then checked outdoor units pressures, amp draws and capacitors. Washed outdoor coil, system is operating properly at this time.
Residential spring system maintenance near Frank Beverly Park. Checked inside units electrical, mechanical and safety components, checked amp draws, duct work, Changed out customer supplied filter, and blew out drain line. Checked outdoor units pressures, capacitors and amp draws all checked out good. System has a hard start already. Washed outdoor coil. Customer happy on departure.
Spring Residential HVAC service call in Plano to perform a system maintenance. Homeowner has two systems, only wanted downstairs checked. Checked inside units electrical, mechanical and safety components. Checked amp draws and blew out drain line. Checked outdoor units pressures, and amp draws. Everything checked out good. Washed outdoor coil. Customer happy on departure.
Spring Air Conditioning Maintenance Service for a residential customer. Performed a one system maintenance checking cooling, checked inside units electrical, mechanical and safety components, checked amp draws, filters UV light and drain lines. Checked outdoor units pressures, amp draws and capacitor. Washed outdoor coil. Everything is operating properly at this time. Recommended changing out filter and adding a start assist to condenser. Customer pleased on departure.
Spring HVAC Maintenance Service for a Residential customer in Plano. Came out for a 1 system maintenance zoned up and downstairs. Checked Amp draws, checked electrical connections, checked blades, checked bearings, checked pressures, checked coil, and checked the drain to complete the routine maintenance. Customer happy on departure.