He knew what to do and he got it done! After 3 days with no heat, we really appreciated his expertise!
Excellent service and excellent customer service
Changed out stat under warranty as unit is a new install. Put it simple easy to use honeywell.
I found power had surged and tripped up the truck stat. I reset power and unit began heating properly.
Changed april air 410 filter
Completed 2 system fall matience. Checked filters, voltages, amperages, safety switches and operation. Units are operating properly upon departure.
Take photos of outdoor unit
Found failing condenser fan motor that was making unit run loud. Covered under 10 and 10 warranty. Replaced fan condenser motor and unit is running quietly and working properly.
Completed 2 system matience on new lennox units both are less than one year old at this time. Filter on kitchen unit will need to be changed early during spring matience. Both units are working properly at this time. Kitchen side delta t is 76/103 Bedroom Side delta t 72/104 Pictures attached
Dispatched to unit with blown fuse. Upon arrival the 30 amp fuse inside the disconnect box had blown after changing an estimated 2 months prior. I preformed a check on the system and all is now in good working condition. No reason for the fuse being blown was found.
Air conditioner repair on Trane system.