Check wiring connections made sure all was correct ... no lose connection's... blowed drain line.. we had no extra thermostats on truck told customer if thermostat malfunction again to take a picture of it.... thermostat may need to be replaced if problem persist.
Spring maintenance, cool and heating working, thermostat a little buggy, raplcement warranty pending, need to reschedule to return.
Water is weeping from base of toilet due to faulty wax ring. Floor is buckli g and will need replaced before we can set the toilet.
Converted furnace to lp. Also programmed thermostat
Completed two system air handler fall matience. Both units are operating properly at this time.
Completed one system fall matience left estimates, unit is heating properly at this time.
Dispatched to unit not running inside or out. As soon as I got to the call I dropped the temperature and called for cooling. And unit started running after delay. I preformed matience check on system and no problems were found. Delta T I'd 83/66.
Summer maintenance performed. 10 year P and L.
Heat load and free estimate on replacement system