Diagnostic work found an existing Taco 6 zone low voltage valve control panel was damaged as a result of a lightning strike. One zone is still working, however the panel sustained damage and will not allow any other zones to work. Chud has provided a quote to replace the panel. It is possible that zone valves may have been damaged, but very unlikely if the heater was off during the storm. Chud will complete preventative maintenance after repair to ensure no other issues are present. ***Gas and power shut off to boiler until we return to repair boiler.*** Weil McLain GV90PLUS, CP7078566.