Performed preventative maintenance on 2 carrier AC systems. Replaced MERV filters provided by the customer. Tested both units evaporator coil pans for proper drainage. Tested condensate pump on basement unit. Temperature split is at 20° For both systems. Both units have the proper refrigerant. The amperage readings are both within then proper amperage rating for these units. Systems are both operating properly at this time.