Came out today for a no ac call. Upon inspection I found that the system would call for ac but the condenser would not turn on. I opened the panel for the condenser and found that the capacitor was extremely bloated . I replaced the capacitor and turned the power back on. The fan for the condenser turned on but the compressor will not operate. The amp draw for the compressor is at a 0. The compressor is seized and will not operate . The system is 17 years old and should be updated. Goodman system model #Ck241b, serial #9605019932. I will reach out to Michelle with all the details.