Came out today for a no AC call on a Lennox system. Upon inspection I found that the low pressure switch was tripped. I connected my gauges and reset the low pressure switch. I noticed that the system was slightly low on refrigerant. I added 2lbs on 410-A and the pressures are now within normal range. The temperature split is at a 20 and the system is operating properly at this time.