Apartment #2203. No ac call. Circuit breaker tripping immediately once contactor is engaged. Verified circuit breaker stays on for heating and fan only. Amperage reading on â€œrunâ€ leg is drawing 1.6 amps even when there is no call for ac. Pulled chassis and confirmed compressor is shorted. See estimate for repair details. ****BILLOUT DIAGNOSTIC**** Took at look at Clubhouse unit disconnect. The â€œstabâ€ accidentally broke and we will schedule to replace the disconnect early next week. We will also wire the blower motor back to the furnace control board in preparation for heating season. Today I hardwired the disconnect temporarily to restore ac since this conditions the gym area also in the clubhouse.