Completed transition from supply plenum to supply trunk. Attempted start up and discovered red thermostat wire was shorted out. Used green fan wire in its place. Management is aware of the situation. Will leave system wired as is, alternative is to pull new low voltage wire to thermostat. Cycled and tested, system working properly at this time. Bill out.