No heat call. Unit was miswired and had to contact National Comfort technical department since the schematic was worn off of the unit. Corrected wiring issues including one leg of power connected to the load switching side of the single pole contactor. Had to install a new contactor due to existing being pitted. The system fan worked in air conditioning, Just not for fan only and heat. The system is now working correctly and tested for proper operation.