Preventative maintenance check up on Lennox HVAC system for heating season. Tested drains and replaced customer supplied air filter (18x20x1), inspected indoor and outdoor coils. Tested voltage and amperage readings on all components. Confirmed proper high and low voltages. Tested the electric heat kit for proper heating. System is operating properly and ready for the season.