John is very well qualified and conscientious in his work. Always polite and never leaves a mess.
John Murphy is very capable and conscientious. He works quickly and effectively on our HVAC equipment. We have total trust and confidence in John.
John replaced the upstairs WiFi thermostat got it working within an hour. He was at our house in just over an hour after the call. Can't Thank Classic or John enough for that kind of service.
Cleaned furnace and checked system function. Drained surge tank for improved pressure control.
I found blower motor having trouble starting. Found run capacitor very weak: 46% low, causing low starting torque. Also, Blower motor bearings have play. Worn. Customer declined this repair. Also, the furnace in need of cleaning. Cleaned & checked gas furnace per new maintenance plan. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Checked filter. Replaced weak capacitor. Set speed and test. Blower: 4.0A . Inducer: 0.89A . Temperature rise: 56 . Supply: 124 . Return: 68 .
Complaint: customer has had to turn the heat up higher than usual. Also, seems to blow air thats not very hot. Found control board logged fault codes 2 to 3: pressure switch failed to close. Cleaned out pressure port on inducer. Thermostat reads high +1. Calibrated thermostat. Set manifold pressures. Set lower speeds. Covered filter opening. Turned up humidifier to 40. Tested operation.
I replaced broken ignition electrode. Set spark gap to 1/4 inch. Tested light off. Boiler lighting smoothly. Checked combustion blower: .3 A. Supply: 104. Return: 80.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced MERV16 air cleaner media. Clean and check humidifier, replace pad, checked water flow and drain. Blower: 1.7/2.3A . Inducer: 0.07/0.24A . Gas pressure: 1.7/ inches water column. Temperature rise: 50 . Supply: 122 . Return: 72 .
I replaced three wire safety pilot for Bryant boiler. Installed new pilot tubing and fittings. Safety switch closed after 53 seconds of lighting. Boiler operated for about 15 minutes and new pilot assembly failed!! Had new pilot assembly picked up delivered. Replaced again and tested operation. Safety switched closed after 20 seconds. Cycled pilot on and off. Working OK.
I turned humidifier back on and checked for leaks. Not leaking at this time, but found where water had been trailing out of frame. I cleaned distributor tray and scale separator frame. Replaced water panel. Tested operation. I increased gas pressure for stage one. Set cycle rate. Calibrated thermostat. Was+5.
Cleaned & checked condensing gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced air filter. Replaced thermostat batteries. Blower: 2.6/3.4A . Inducer: 0.25/0.47A.
Picked up keys from 707 N 2nd St. Unit C: Goodman 2123: I found electric furnace with bad transformer. I tested controls and wiring for shorts and found none. Also found evaporator coil very dirty. System running without a filter. I tested for shorted and grounded controls and wiring. Found none. I replaced transformer with fuse. Check control circuit amps for cooling and heating modes: 0.45 A. I clean evaporator. Replaced air filter. Unit D: checked to see if heat is operational. Found heat was working and set at 58. Dropped off keys at 4564 Chouteau.
3600 Hereford Street, 1N: Installed new heat kit package. Installed new fan control board. Tested operation. Amp draw: 34.7. Voltage: 242. Supply air: 109. Return air: 73. I set up a thermostat for “non-heat pump“ to defeat time delay. Balance due: $515.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced air filter. Blower: 3.8/4.7A . Inducer:0.09/0.21A . Gas pressure: 1.9/3.6 inches water column. Found basement pressure negative (-.006 inches water column) due to leaks in return-air ducting. Suggestions: return ducting air leaks can be sealed with caulk and tape. Keep basement door open for make-up air to keep pressures balanced. Set fan to “auto“ position when in cooling mode for proper humidity control. Recommend whole house humidifier installation: $716. 15% PMA discount applies.
I installed a base pan heater for mini split system to keep ice from building up at base of unit. Tested system operation. AH 9052: supply: 106. Return: 74. AH 9085: supply: 106. Return: 76. Suggestions: Must lift remote from holder on the wall to use. Listen for beep at unit to confirm changes made at remote controls.
Found burnt wire, dirty air filter, and weak blower capacitor. Replaced burnt wire. Replaced air filter. Replaced blower run capacitor. Clean and check electric furnace per maintenance plan purchase. Tested heating elements. Tested sequencers. Supply: 106. Return:65. Amps: 42. Checked temperature rise. 41.
Cleaned & checked condensing gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced air cleaner media. Clean and check humidifier, replace pad, checked water flow and drain. Blower: 2.5/3.4A . Inducer: 0.26/0.44A . Gas pressure: 1.9/3.6 inches water column. Flame: 12uA. Set humidifier blower speed. Calibrated humidity reading.
found leak water at condensate pump. Found discharge fitting chewed up by a mouse. Need to replace discharge check valve Fitting. Follow up: need to order three eights discharge check valve for condensate pump.
Found condensate pump float safety tripped. Pump not able to pump water through frozen line that goes to the outside. Humidifier was installed last year and connected to this existing condensate pump system. Condensate pump system works for warm weather only. No charges today. Suggestions: run new condensate discharge line over to drain stack where washing machine drains.