Jeremy was very friendly, polite, knowledgeable, and helpful.
Jeremy Neal was great! We couldn’t have asked for better service! Thank you!!!
Professional, personable and informative without being pushy
Jeremy was professional, knowledgeable, and solved our problem efficiently. I would definitely use him again.
Fast and efficient workers
You should keep him.
Thank you for your help and keeping us updated with the status of our heating issue. it was much appreciated. Price I can't comment on as this is paid by someone else, but our Tech was so helpful.
Had a problem with our heater and he figured out the problem and fixed it.
Prompt and productive service with a wonderful attitude and thankfully some explanations as to what was actually causing the problem.
Diagnosing a heat pump!
Nest thermostat repair in Chico
Maintenance on a heating system.
Winter maintenance on a furnace.
Lunch break at your moms house
Heat maintenance at your moms house
Assessing the replacement of a gas heater.
Thermostat not working on a heater in Oroville.
Furnace maintenance on a day and night gas package unit in California park
Performed an annual heating maintenance on a Bryant package unit!
Performed heating maintenance on attic RUUD 90% gas furnace. Checked amperages on indoor blower motor, inducer draft motor, and capacitor. Checked voltage and ensured proper fuse conditions and mechanical operations. Checked flame sensor, pressure switch, and gas line along with ductwork. Checked burners and flames to ensure a good flame. Checked temperature split and thermostat functionality. Changed both filters inside. System heating and operational at this time. Serviced customer on W 11th Ave in Chico, CA.
Performed a heating maintenance!
No heat in Gridley.
Filter change and maintenance.
Performed heating maintenance on attic 80% gas Lennox furnace. Changed filter. Checked capacitor for indoor blower motor and found it to be low, after customer approval I replaced capacitor to bring system to its most efficient state and to prevent blower motor from going out. Checked amperages on indoor blower motor and inducer draft motor. Checked voltage and burners. Checked pressure switch, flame sensor, and other safeties. Checked temperature split and thermostat functionality. System heating and operational at this time. Serviced customer near Forest Ave in Chico, CA.