Climate & Energy Solutions installers, Jonathan and Cody, came as expected and completed the installation, cleaning up thoroughly before leaving. Jonathan also took the time to explain the steps of the installation and the remote controls to us before leaving. He offered to answer any questions I might have. I felt assured that I was in good, knowledgeable hands.
Technician was very friendly and professional. We will definitely use again.
Heat pump two wall mounts
Day & Night condenser split system. Ac repair cooling maintenance. Coil wash. Filter check. Amp check. Temp split.
Evaporator coil was impacted with dirt, and filter was easy for a change. Removed filter and cleaned coil. System is now cooling well at this time with a temp split of 15°. Capacitor: 44.6/5uf Compressor: 12a Fan: 1a Split: 81-66, 15°
Performed preventative cooling maintenance on outdoor Bryant AC package unit. Changed indoor air filter. Checked the following: -Amperages on compressor and outdoor condenser fan motor. -Dual run start capacitor for the compressor and fan. -Contactor and proper voltage. -Refrigerant circuit for proper flow. -Thermostat functionality. -Proper air flow/temperature split from supply and return vents. System is cooling well at this time with a temp split of 20°.
Performed preventative cooling maintenance on outdoor Carrier condensing unit. Checked amperages of compressor and outdoor condenser fan motor. Checked dual run capacitor to ensure proper microfarads. Checked voltage and ensured proper disconnect conditions. Checked refrigerant flow and mechanical operations outside. Washed outdoor condenser coil. Changed both indoor air filters. Checked temperature split between return and supply. Checked thermostat functionality. System cooling and operational at this time. Serviced customer on Windham Way in Chico, CA.
Diagnosed a faulty inducer assembly on a Nordyne furnace!
Diagnosing a Gree Minisplit with refrigerant leak.
Repairing an AC condenser!
Fixing an AC condenser!
Cleaning a condenser coil!
Fixing an AC system!