Complete 1 system A/C repair and preventative maintenance check. found the system running well with no issues at this time. Filter is clean. Cleared drain line. Checked all safety switches. Blower wheel is clean and electrical components inside and out are running good. Pressures are good. System running with no compressor saver or surge protector that can lengthen the lifespan of system and reduce power bills. Also system is running with just standard one in filter. Needs electrostatic filter to better clean the air and keep system and house cleaner longer. Also needs UV inhibitor to get rid of current growth inside system and prevent new growth from happening to keep residents healthy.