Cockroach took out hermetic side of capacitor, replaced 45/5 capacitor and compressor cut on fine. Hard start could be added to help prolong compressor life. Contactor is in fair condition. Coil is dingy. Systems pressures are good 145/320. Indoor coil is clean. 19x54x1 filter is clean. Blower is a bit shaky. Blades are clean. Furnace interior is in good condition.