Found system not working, heat pump not getting signal, necked for low voltage short, finally got Tomâ€™s help and figure out the system was empty of Freon, and and on low pressure switch lock out. Set lead for consultant to come out for estimate.customer does not have an email address
Installed lp kit on main floor furnace. System install complete. 7 system maintenance plan included in install price
Installed new Rheem 20 SEER system with 96% furnace.
Found blow out the leak in the outdoor unit. Michael has chosen to replace the whole main floor system. Scope of work filled out and deposit collected. Please call 770) 861-3142 to schedule install. Order Econet Rheem thermostat with equipment as well
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at firstname.lastname@example.org or call us at (770) 932-5012.
Furnace repair call. Thermostat software had issues that were resolved with Nexia. Thermostat dead band kicking on in less than 1°. Homeowner getting with reliable to get reimbursement on thermostats.
Estimate for duct cleaning and dryer vent cleaning. Basic cleaning of the two new Rheem systems in attic. Clean the main dryer vent but not the basement dryer vent.
No heat on heat pump. Outdoor fan motor bad. Replaced motor. Compressor had a hard time starting but finally started up. System operation normal at this time
Supplied and installed 2 Rheem 20 Seer Heat Pump Systems with econet zoning.
Customer getting 2-20SEER heat pump systems located in the attic and on the right side of the house. Pull down stairs are 22 inches wide from the springs. Installers bring A LOT of drop clothes. Pay extra special attention to detail with this install. Jeff is to be on site all day for the install. Units marked 5 and 6. Customer name is Michael.
Added dedicated transformer to zoning and tightened damper down. Airflow reading 0 with bathroom zone calling
Free consultation regarding replacing existing 4-ton unit. Addressed ductwork and IQA. Thank you for your time. Estimate valid for 30 days, for any questions contact us at (770) 932-5012 or online at https://comfortcontrolinc.com/