Comfort Control has been my go to company for A/C and heating repairs and installation for about the past 7 years. Their response time is great, prices are quite reasonable, and they’re incredibly honest...a rarity these days. And the technicians they’ve sent out have always been top notch. Vu Tran is outstanding. He’s of the main reasons I’ve never looked for another company besides Comfort Control. He’s super friendly, professional, incredibly knowledgeable, trustworthy, and honest. This time around, I was also introduced to Chris Sutherland, another tech with the company. Like Vu, Chris was fantastic and I was super impressed with him.
The technician was efficient and I was able to get a service date quickly. He asked if I had any questions and showed me how to change batteries on my thermostat.
Ta has been impeccably servicing/maintaining my HVAC for about 12 years. He's the best!
Look forward to using him in the future.
On time with friendly staff
Ta cannot be beat for quality work done with a friendly and professional attitude. Thank you!
Ta and the service he performs twice a year for my HVAC are superb. He's knowledgeable, courteous, and friendly - a rare combination in these days and times. Thanks so much Ta!!
Ta has been servicing my HVAC for about 6 years and he's wonderful! - thorough, professional, knowledgeable, and personable; going above and beyond my expectations - a rare combination in these days and times. Thank you so much, Ta!
Comfort Control helped me out during a bind when my A/C unit stopped working in the scorching heat of July. They made every effort to come as quickly as they could and fixed the problem with great service and communication!
I always enjoy my maintenance visits from Ta. He's professional, knowledgeable, and very courteous. Please give him a raise for his outstanding work!
Replaced fan relay fan came on moving air threw the house. Unit is cooling at this time.
Arrived on site, found a bad blower motor relay, unable to replace because supply store is closed and I donâ€™t have one on my truck. However Comfort adviser will be coming out Monday 3/30/20 to give quote on new equipment.
Sign 1 comfort control membership. Complete 1 system a/c repair and preventative maintenance check. Find a 5-year-old evaporator rusted. Find condenser compressor capacitor bad, replace capacitor under full warranty. Install pureAireX air purifier system to kill molds and improve air quality. Did not change the filter. System operating at this time.
Complete 1 system a/c repair and preventative maintenance check. 2 4" ductwork in the ceiling has to be changed out due to water damage. 2 10" section duct might have to be repaired, the supply & return air box has water damage from water. Found control board send a signal to the gas valve and sometimes does not. Wires also connected to gas valve and could be damage. Tested blower motor and possible damage to motor winding.
Complete 2 system furnace repair and preventative maintenance check. Check both furnace components and all normal. Attic does need more insulation and downstairs system needs water safeties. Also recommended ultraviolet system for IAQ. Emailed estimates to Martha as she wants to think over them
Complete 2 system furnace repair and preventative maintenance check. Replaced Upstair filter and main floor media air cleaner. Checked electrical and safety switches all ok at this time. Did a combustion test and all within range. Both furnaces heating normally.
Complete 2 system furnace repair and preventative maintenance check. Did not change filter, check safety and operations. Find both furnaces operating within manufacturer spec. Both system missing in line water protection and surge protection for the system. Suggest air purifier system to improve air quality and prevent molding. Customer not home.
Complete 1 system furnace repair and preventative maintenance check. System heating at this time but is 27 yrs old. With a weak blower controller. The blower itself is extremely dirty and unbalanced with signs of oil leakage. The ac system is the same age and the refrigerant will not be available next year so the system would not be repairable. Due to age and condition, I recommend the replacement of the system.
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at email@example.com or call us at (770) 932-5012.
Complete 1 system furnace repair and preventative maintenance check. System from 1998. The customer wants a consultation for replacement. Sending Garrett out for a free consultation.
Complete 1 system furnace repair and preventative maintenance check. Turn on the system to heat and heating normally. The system is a 1992 model and needs to be replaced. Will have the manager come out to evaluate the system. Lots of rust inside the heat exchanger.
Complete 1 system furnace repair and preventative maintenance check. Replaced filter. Found system running very high carbon monoxide. Over 100 ppm. Recommend having the gas valve calibrated. Calibrated valve and brought levels back to the safe operating range. The system is old but heating well.
Complete 2 system furnace repair and preventative maintenance check. Changed filters. Added drain pan treatment into systems. Tested mechanical and electrical components. Found gas valve in the main level system running at high amps and weak blower capacitor (5uf). Main level system has no overflow protection. Upstairs system heating with no current issues. Found downstairs evaporator coil with bacterial buildup, cleaned evaporator coil. Systems are heating at this time.
Complete 1 system furnace repair and preventative maintenance check. Renewed comfort club membership. Replaced filter, checked electrical and safety switches all ok at this time. Did a combustion test and all with range. System is heating normally.