Fast and professional service!
Did a great job, and was very personable
I have never had a bad experience with your employees. They are always helpful, pleasant, and friendly.
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at firstname.lastname@example.org or call us at (770) 932-5012.
Renew and complete cooling preventative maintenance check. Find cooling system operating within manufacturer spec. No concern at this time. Change filter customer provided. Check the drain and clean the A/C coil. Suggest compressor hard start kit t improve start-up and reduce the load.
Complete 1 system a/c repair and preventative maintenance check. Replaced air cleaner provided by the owner and clean dirty condenser coil. System is cooling normally. Replaced disconnect box and install a surge protector for ac system. Tested and working normally.
1 system heating preventative maintenance and renewal. Air cleaner working well. Checked the electrical and safety switches. All are okay at this time. Installed an APCO UV light system to prevent bacteria, mold, air born viruses, and to improve indoor air quality. The system is heating normally at this time.
Completed 1 system furnace repair and preventative maintenance check. Changed filter and water panel provided by the customer. Changed Apco UV bulb. Tested combustion and found co and oxygen levels within range. Components are in good shape. The system is heating normally at this time.
1 system tune-up and preventative maintenance check. Please make note of filter size. Ultravation 20 x 25 x 5. System cooling normally at this time.
Performed 1 system cooling maintenance. Added bleach tablets. Changed filter. Chemically cleaned outdoor unit. System operating properly at this time and ready for the summer.
1 system furnace tuneup. Replaced filter, checked electrical and safety switches all ok at this time. Found worn ignition and weak flame safety sensor, but working at this time. Suggest to replace next fall time. Did a combustion test and reading over the carbon monoxide safe zone. Calibrated system to safe operating condition. System is heating normal
1 system furnace prepaid pm. Air cleaner is good, checked electrical and safety switches all ok at this time. System is heating normal
Replace humidistat #60 and Re-wire control. Humidifier operating at this time. Clear clogged valve.