CC always goes above and beyond!
Was very happy with the service
R routed flex duct to the living room for better airflow.
Complete 2 system a/c repair and preventative maintenance check. Cleaned outdoor units and checked all components. Main level system operation normal. Did not. Hinge filter as it is a 5" filter and I do not have those on my truck. Recommend adding surge protection, compressor saver and up light to prevent mold from growing in the system. Sun room u it still has all the same issues as before but homeowner stated that he's just waiting on it to die
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at firstname.lastname@example.org or call us at (770) 932-5012.
No cool. Found system with low Freon and phaseout unit. Found rusty coil, supply plenum is not insulated and rusty. Found outdoor system draws high amps 12.3 of 18 rated amps at 72 degree outdoor temperature. Found burnt/pitted main electrical switch. System is old and needs to be replace. For repair option, replaced burnt switch, add Freon, needs compressor saver to reduce stress on startup.
Renew the Comfort Club Membership plan and completed cooling preventative maintenance check. Change filter customer provided. Check the drain and cleaned the A/C coil. Suggest hard start kit to help improve startup and reduce the load. System missing breaker box. Need to install a breaker to meet code. System operating at this time.
Furnace repair call. Issues started around the same time customer changed his thermostats to ecobee. The customer wants to change thermostat back to see if it solves the issue before moving forward with changing dampers.
Completed 2 system furnace repair and preventative maintenance check. Found outside package unit to be running with in manufacture spec. Found inside the furnace to have out of code gas line and no secondary water safety device. Recommend repiping gas line and installing secondary water safety. Systems running at this time.
One system prepaid heating maintenance on the heat pump
Furnace repair. Checked and found that the inducer motor was locked up. Removed the clog and cleared the tubing. The system is now operating at this time. The tech was out on 10/19/2018. This was a warranty service call. No charge to the customer.
One system a/c repair and tune up complete. Found weak blower motor controller (5 uf) putting a strain on the blower motor, recommend replacing the part. Found no water safety, recommend adding on. The system is 13 years old, recommend adding hard start kit to take a load off of the compressor to help it run smoother and last longer. The system has no surge protection, recommend adding on. Chemically washed condenser coil. Replaced blower motor controller, installed water safety, installed surge protection on furnace and condenser and installed hard start kit. The system is cooling at this time.
No cool. Found clogged filter, main switch makes a lot of noise. Replaced main switch and installed compressor saver to system. Has weak starter but will replace next spring time. System is cooling at this time
Found bad pressure switch. Changed pressure switch and system is heating at this time. Warranty.
Renew and complete 2 cooling pm check. Did not replace system filter, replace sunroom system filter. Find main system operating normal. Adjust damper to help balance house air flow to improve comfort. Suggest surge protection for out door unit and suggest APCO Air purifier to help prevent molding and improve air quality. Find sunroom system operating but have lot of worn parts due to age. Fan motor not balance and making noise, compressor operating stress with high amp, dirty duct system, rusted coil, and pitted contactor. Due to system suggest to upgrade system and not repair. Both system operating at this time.
1 furnace pm check complete. Changed filter. Tested static pressure, its reading 1.01 w.c. When max static pressure for furnace is rated for 0.5 w.c. System's return air is under sized. System has no water safety and is therefore not up to code, recommend adding on. Found dirty blower wheel with pieces of foam stuck on wheel. Removed foam bits but I do recommend a deep clean on the blower wheel/ assembly. High static pressure is causing the motor to operate at a high amp draw. Gas valve is operating at a higher than maximum amp draw. Found rust on evaporater coil. Due to age and condition of furnace, recommend upgrading to a more reliable, more efficient furnace. Also the heating/ cooling systems are mismatched. Evaporater coil is a c width coil (21 inches) and furnace is d width (24.5 inches). System is heating at this time.
No heat. Check and find customer replaced his tstat with ecobee tstat and was not set up properly and wire wrong for zone 2 tstat. Help setup tstat and remove O for zone 2. And heating system operate. Test and find heatpump system operating with faulty voltage absorption system and molded airhandler. Complete cleaning for evaporator coil airhandler assembly and complete voltage absorption renovation HN4C with performance enhancement added to help system start up better and reduce load. System operating at this time.