Was very happy with the service
Found bad pressure switch. Changed pressure switch and system is heating at this time. Warranty.
Renew and complete 2 cooling pm check. Did not replace system filter, replace sunroom system filter. Find main system operating normal. Adjust damper to help balance house air flow to improve comfort. Suggest surge protection for out door unit and suggest APCO Air purifier to help prevent molding and improve air quality. Find sunroom system operating but have lot of worn parts due to age. Fan motor not balance and making noise, compressor operating stress with high amp, dirty duct system, rusted coil, and pitted contactor. Due to system suggest to upgrade system and not repair. Both system operating at this time.
1 furnace pm check complete. Changed filter. Tested static pressure, its reading 1.01 w.c. When max static pressure for furnace is rated for 0.5 w.c. System's return air is under sized. System has no water safety and is therefore not up to code, recommend adding on. Found dirty blower wheel with pieces of foam stuck on wheel. Removed foam bits but I do recommend a deep clean on the blower wheel/ assembly. High static pressure is causing the motor to operate at a high amp draw. Gas valve is operating at a higher than maximum amp draw. Found rust on evaporater coil. Due to age and condition of furnace, recommend upgrading to a more reliable, more efficient furnace. Also the heating/ cooling systems are mismatched. Evaporater coil is a c width coil (21 inches) and furnace is d width (24.5 inches). System is heating at this time.
No heat. Check and find customer replaced his tstat with ecobee tstat and was not set up properly and wire wrong for zone 2 tstat. Help setup tstat and remove O for zone 2. And heating system operate. Test and find heatpump system operating with faulty voltage absorption system and molded airhandler. Complete cleaning for evaporator coil airhandler assembly and complete voltage absorption renovation HN4C with performance enhancement added to help system start up better and reduce load. System operating at this time.
Renew CCI plan and complete heating pm check. Find lennox 11 year old furnace operating normal, find flame safety weak and worn. Find furnace producing high CO level of 68 PPM. Suggest combustion calibration to help reduce CO level and improve efficiency. Suggest replacing flame safety to prevent failure. Find gas line and flue pipe not up to code. Customer do not want repair at this time. Heating system operating at this time. Change filter customer provided.
Completed maintnenace on 2 units. A/c solutions installed new unit for main floor approx. 9 month ago. Has bad condensate pump, replaced pump under warranty and everything operating normal at this time.
Amana 3.5 Ton 14 seer $2979.00 ASX140421 UNIT 10 Year warranty parts 1 year warranty labor $429.00 OFF DISCOUNT PER TOM Install asx140421 unit. Pressure test and charge system to manufacture spec. System operating at this time.
No cool. check and find system disconnect box was off. Check and find system empty of charge. Check and find system leaking at condenser unit coil. System coil under warranty. Sold customer new amana ac unit to be more efficient and more reliable. Need to schedule to come back and complete job for $2550.00
1 system ac tune up complete. Did not change filter. Added chlorine tablets to evap coil drain pan to help keep drain line clean! Evap coil is rusty. Checked mechanical and electrical components of system, all operating within manufacturer specifications. Refrigerant levels are good. Chemically washed condenser coil and applied rust proof waxing. Recommended adding performance enhancement system to take a load off of the compressor and prolong the life of the system. Recommend apco air purification system to keep evap coil clean, prevent mold, and kill bacteria and viruses for overall better air quality. System is operating normal at this time.
No cool. Check and find system operating with very dirty filter, replace filter with aprilaire 610. Check and find 2 year old system operating with low charge due to loose connection at service cap. Tighten connections and recharge HJ8A to manufacture spec. System operating at this time. Suggest plan to help maintain system.