CC always goes above and beyond!
Was very happy with the service
Complete 2 system a/c repair and preventative maintenance check. Cleaned outdoor coils and checked all components. Main house system operation normal. Sunroom mini-split has leak in refrigerant line and system is almost out of charge. Need to send install crew back out here to fix. May need to replace lines
Complete 1 system a/c repair and preventative maintenance check. Changed filter. Tested mechanical and electrical components. Found dirty blower wheel. Found system slightly low on r410a. Gave quotes on iaq products. Customer is going to have iq air filter installed. Return plenum is 22x28. Return has four 8" ducts and one 12" duct. Customer prepaid for iq air filter. Pulled and cleaned blower wheel. System is cooling at this time.
Complete 1 system a/c repair and preventative maintenance check. Change 18x20x1 filter, check drain and operations. Find system low on charge, recharge system to manufacturer spec. Find evaporator coil rusted and need to keep check. Suggest in-line water protection for Airhandler.
Completed 1 system preventative maintenance. Tested the electrical and mechanical components of the indoor portion of the system. Found all electrical components in good shape. The system has a compressor saver along with back up water safety. I do recommend an ultraviolet system to be installed in order to improve indoor air quality, protect against viruses, and combat common mold growth inside units. Both indoor and outdoor components have surge protection. Cleaned outdoor coil and checked all electrical and mechanical components. Brand new system is operating normally at this time.
Complete 1 system A/C repair and preventative maintenance check. The system not operating. Test and find Amana furnace control board fail and not operating properly. Give customer estimate to repair system. The customer wants to wait. The customer wants to look over her options.
Complete 1 system furnace repair and preventative maintenance check. Check and find a heating furnace operating at this time. The customer stated that the furnace failed last night and come back in the morning. No error code on the furnace. Check safety and operations and find furnace operating at this time. Concern furnace control boards may not operating normally but do not detect problems at this time. May need to replace the control board for the upstairs furnace. Give customer estimates.
Tech replaced inducer assembly 12/9/2019 and now not heating again. Check and find inducer assembly tube bend causing pressure restriction. Repair tube and system operating but flame sensor also bad reading .4/1.5 rated. Replace sensor for the upstairs system. System operating at this time. Find downstairs system operating but CO level reading over 3000 ppm and detector lockout on safety. Find furnace in exchanger badly rusted and system not burning properly causing dangerous co level. Shut system off. Run system for about 20 min and the house already reading 40ppm in house. Not safe to operate. Due to bad heat exchanger, we need to replace the system.
Complete 2 system furnace repair and preventative maintenance check. Homeowner just wanted a technician to explain everything on his new systems. Did not want maintenance
Complete 2 system furnace repair and preventative maintenance check. The main system operation normal. The sunroom system needs to be replaced. Please schedule Garrett
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at firstname.lastname@example.org or call us at (770) 932-5012.
Complete 1 system furnace repair and preventative maintenance check. Found system with a fault code. The code was for locked rotor. Reset the system and was able to check. Found nothing wrong. Added a start kit to the condenser. Cycled system a few times and started up every time. Talked to customer about the Dehumidifier. He agreed and will do in the spring along with a membership.
Complete 1 system furnace repair and preventative maintenance check. Tested system operation. Ran system for 40 mins nonstop. Subcool 12, superheat 8, delta 20. Also tested heat and heat operation normal. Could not find any issues with system other than filter pretty dirty from construction.
Complete 1 system furnace repair and preventative maintenance check. Find a heating system operating with manufacturer spec. No concern at this time. Change filter customer provided.
Complete 1 system a/c repair and preventative maintenance check. Tested system and everything is working normally. I'm getting 8 degrees to superheat and airflow is at 1200 cfm on 2nd stage cooling. Was getting about 70-71 degrees in the room and nest thermostat was reading 76. The room was around 58% humidity. Need to lower the humidity to feel more comfortable.
Complete 1 system furnace repair and preventative maintenance check. Renew Comfort Club membership. Replaced filter and UV bulb. Checked electrical and safety switches all ok at this time. Tested heat strips and working normal. Installed compressor saver to help on startup of the compressor. The system is heating normally.