Was very happy with the service
1 system ac tune up complete. Did not change filter. Added chlorine tablets to evap coil drain pan to help keep drain line clean! Evap coil is rusty. Checked mechanical and electrical components of system, all operating within manufacturer specifications. Refrigerant levels are good. Chemically washed condenser coil and applied rust proof waxing. Recommended adding performance enhancement system to take a load off of the compressor and prolong the life of the system. Recommend apco air purification system to keep evap coil clean, prevent mold, and kill bacteria and viruses for overall better air quality. System is operating normal at this time.
No cool. Check and find system operating with very dirty filter, replace filter with aprilaire 610. Check and find 2 year old system operating with low charge due to loose connection at service cap. Tighten connections and recharge HJ8A to manufacture spec. System operating at this time. Suggest plan to help maintain system.