Complete 2 system furnace repair and preventative maintenance check. found both blower wheels very dirty. Upstairs blower capacitor very low on power. Both systems have a concerning amount of mold on and inside systems. Neither system has any foe of water safety. Both thermostats are outdated and inefficient. Recommend blower wheel cleanings to relieve stress. Lower motor and achieve proper airflow for the house. new capacitor for the upstairs system. Inline float switches for both systems to protect the house from any water damage if drain lines ever clog up. New thermostats to get more accurate temperatures in the house. Electrostatic filter to better filtrate the air and keep systems and house cleaner longer and UV inhibitors to clean the air in the house and kill mold, bacteria, allergens, and odors in the house and improve the health of the residents.