Complete 1 system a/c repair and preventative maintenance check. Found heat pump on a low-pressure lockout. Reset the system and found pressures to be normal. The system not acting up at this time. Possible causes of issue could be a faulty txv, a restriction, a faulty defrost board or a faulty low-pressure switch. Found electrical pitting on the main electrical switch. The system is cooling at this time.