Jon is always professional and does a great job!!
Rick was great. He is a good tech and knows how to service the unit. He was very professional and courteous. He worked very quickly and knew his trade. GREAT JOB.
Nobody likes replacing their a/c unit but Jeff helped me understand that fixing my old one was only going to be temporary (my system was old). He went through options on units and options on paying for it. Jeff even brought me two window units so we didn’t have to suffer in the heat until our installation date. The two young men that came to do the installation were extremely friendly, professional, and best of all quiet. The job was done before we knew it and our house is cool again. I can not thank them enough for helping us with this and bringing some comfort back to our home.
Reece was very helpful in solving the issue with our system. Appreciated his expertise and advice.
I was pleased with the professionalism and friendly attitude of the workers at my home. Polite, friendly and caring.
Reese was polite and carefully explained the issues he found with my system.
Great leadership and caring about employees leads to great experience! From first contact, to repairs being completed, nothing but great things to say!
Jordan was very professional and friendly.
Garrett did a great job and worked hard to get us the deal that we could manage.
The technician was amazingly fast arriving and followed through to find the exact problem with the HVAC.
He was very prompt, knowledgeable and friendly. Super helpful
Reece was prompt. Knowledgeable. Kind. Friendly. Very helpful. Awesome.
Jon is very professional and courtesy. He makes sure I understand what he is doing and answers all my questions. He took the time to give me instruction on how to change my electrostatic air filter.
16 seer 4 ton heat pump system 10 year parts warranty 10 year labor warranty Lifetime outdoor unit replacement compressor warranty Supply plenum Return plenum Nest thermostat
Upstairs 8â€ actuator is stuck, unhooked 24v and 8â€ damper is not opening. When system is running off of the upstairs thermostat it is freezing up due to improper airflow throughout the air handler cabinet. Unhooked damper and shook actuator, actuator is opening 80% when shaken. Left actuator unhooked from zone board to allow airflow to the upstairs. Mr. Hewell wants to look into getting actuator replaced after wedding. For now he will leave actuator unhooked and manually open and close when needed.
A/c diagnostic in Jefferson. 2 zone system in the attic. System is cooling at this time. Check all operation as of right now everything is wiring properly. Blower wheel is clean, evaporator coil is clean, filter is good. 2 zone dampers are closing and opening as they should. Outdoor condenser looks good, pressure are good.
A/c warranty repair in Jefferson. Installed new CoreSense diagnostic. System is cooling at this time.
warranty coil and TXV. Changed coil, txv and filter drier. Removed all refrigerant from system pulled vacuum and recharged system to 10 degrees subcool. System operation normal at this time.
No cool in Jefferson. Found system slightly low on refrigerant. Corrected charge to 10 degrees subcool, and the suction side temperature and pressures continued to fluctuate like the TXV was hunting even though the charge is correct. This is an indication of non-condensables in the refrigerant circuit. As well the fluctuation dipped below 32 and just above 32 while the superheat stayed around the 20-24 degree range. Indoor temp is 72. Outdoor temp 80. Recommend removing all refrigerant, replacing the line drier, and replacing the TXV. Pressure test refrigerant circuit, evacuate to 500, and correct the charge. Check to see if parts are covered under the name Paxton. If they are warranty the evap and TXV.
Inspected heat pump system to find it to be slightly low on refrigerant. Mrs. Hansen joined our comfort control membership This will allow us to maintain her system and monitor if the equipment has a leak or was just mischarged.
No cool in Jefferson. Found unit low on charge. Added a pound of r22 to correct the charge. Customer does not want to replace at this time. Moving soon.
2.5 ton 14 seer heat pump only 10 year parts warranty 2 year labor warranty
No cooling call in Jefferson. Arrived to find that upstairs unit compressor has seized. Tried to start it with a new capacitor and hard start kit, but to no avail. Gave options of repair and of replacing. Customer wants to discuss options with his wife.
System not cooling. Found failed outdoor unit dual run 40/5 capacitor. Replaced capacitor. Checked refrigerant levels. System was slightly low on refrigerant. Corrected charge with about 8 oz of refrigerant. System is cooling at this time.
3 ton heat pump 16 seer 10 year parts warranty 10 year labor warranty Lifetime outdoor unit replacement compressor warranty Supply plenum with dampers Return plenums High flow registers Nest thermostat Move thermostat to hallway Increase master return to a 10â€ Increase hallway return to a 12â€ Replace 10â€ trunk to living room with a 12â€ trunk reduced to a short 10â€. Increase 6â€ in kitchen dining room to 8â€ fed with the same application as the living room.
Replaced blower relay in air handler.
A/c diagnostic in Jefferson. Old unit R22 unit was icy up found leak in the evaporator coil. Customer getting new unit.
No cooling in Jefferson, GA Heat pump unit freezing up due to no air flow at the indoor unit. Found blower relay meted at the terminals causing no voltage to the blower motor. Relay needs to be replaced and wires repaired. Bypassed relay to run blower constantly, until relay can be replaced. Checked charge on outdoor unit to find it slightly low on refrigerant. Leak searched indoor coil and was not able to find a leak. Possible incorrectly charged from another company. Corrected charge. Will return with the relay to make proper repairs.