Jon is a great person and has great experience. He finished the job quickly and showed me the problem. He is a credit to your company and deserves a raise:)
Garrett was very helpful answering all of my questions and explaining what our home needs.
Ta explains everything in a way is easy to understand. He shows me everything that I need to know about with the systems.
Seth Delmada arrived on time and was courteous and very professional. We are very happy with our service from Comfort Control.
Found drain clear no algae buildup in pan. Tested pump and found working but sounded very loud and grinding. Recommend replacing pump. Installed new pump. Tested and worked good.
Complete 1 system a/c repair and preventative maintenance check. Cycled system, checked blower components, controller ok, checked amp, wires connections, checked drain line, changed filter, checked ac components, operating pressures, superheat and subcooling, cleaned outdoor coil. The system works fine.
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at email@example.com or call us at (770) 932-5012.
Complete 1 system a/c repair and preventative maintenance check. found the system not cooling properly, due to low charge which client was aware of since Freon has being added yearly. The client made the decision to replace the system, provided a new system estimate. The new replacement is scheduled on Thursday, June 27.
Replaced evaporater coil and filter drier. Pressure tested at 410 psi with nitrogen. Flushed with nitrogen. Pulled vacuum to 500 microns. Recharged system and system is cooling at this time. Coil comes with 5 years part warranty and 2 years labor.
Complete 1 system a/c repair and preventative maintenance check. Found system low on charge. Found leak in the evaporater coil. Ordered new coil from tristate. Will return to replace coil once it comes in.
Complete 1 system a/c repair and preventative maintenance check. Customer is moving shortly so will not be renewing. Found pressures for system very good. System is draining condensate properly and filter is clean. Customer had issue with freezing at evap coil due to dirty filter it is imperative to keep filter clean so that system can breathe. As of now system is running good.
Fan speed was higher than recommend. Switched it to low. Supply temp dropped. System is running.
Completed diagnostic found thermostat malfunctioning. Turning on emergency heat constantly. Switched out thermostat. System running at this time.
No cool upstairs. Check and find Lennox system lock out on high pressure. Reset and find system operating within manufacturer spec. Show customer how to reset Lennox heatpump lockout. Complete 2 cooling pm check. Change 2 filter and clean ac coil. Both system operating at this.
Complete 1 system a/c repair and preventative maintenance check. Found blower clean and capacitor good. Changed filter and cleared drain line. Found outside unit electrical components good. Good amps on compressor and fan. Cleaned off condenser fins and recommend surge protector and hard start kit for outside unit. System running at this time
1 system A/C tune-up. Left filter for the owner, cleared drain and clean condenser coil. I could not hear whistle noise/cricket noise. Only thing is some vibration in the walls in the bedroom. The owner told me about the dirty sock syndrome smell. I could not smell it and owner state it's only in heating mode. My only suggestion is installing APCO in the light system in the coil and the supply plenum. System is cooling at this time
Completed one system maintenance. Found both systems to have very dirty blowers and the upstairs system is showing signs of possible mold growth. The downstairs system to had a failing run capacitor. Also, the main level system was low on refrigerant. Filled the mail level with refrigerant and both systems are running.