Vu did nice work in rerouting an HVAC duct in my basement to allow conversion to a small office. Work was done promptly with due consideration for surrounding personal effects and tools. I enjoy working with Vu, Tom and all of Team Comfort Control !
Reece has been here before. Knew where everything was & did his job in the attic then outside. Explained to me what he had done & why. Thank you, Reece.
Reece Wilson is the best:)
Technician was very professional. He explained everything I needed to know.
â€¢Prepaid heating maintenance in Jefferson Georgia. Checked the heating integrity. Checked safety. Checked heating elements and motors . Changed air filter . System is heating at this time . â€¢Biological growth is growing in the air boxes . Would highly recommend a UV light to kill and prevent the growth from spreading . â€¢Would highly recommend the drain line have a overflow water safety device to prevent clogged drain lines/ water damage. â€¢Outside start up contacter is getting pitted and has burn marks would suggest replacing that part to prevent future break downs. â€¢Outside dual start cap is weak and below rating would suggest replacing to prevent future issues. â€¢Will send over recommendations with prices to the email on file .
One system heat maintenance in Jefferson. Arrived on site, changed filter and checked heat kit, checked electrical connections, amp draw and capacitance. Unit is operating normally at this time. Recommended installing air purifier to system to improve indoor air quality and prevent organic growth inside system
Heating maintenance Jefferson. Completed maintenance on new system. Everything installed properly. System is heating properly. Static pressure is good. Everything inside is clean. Changed filter.
Signing family up for the maintenance program in Jefferson Georgia . Going to complete heating maintenance today . Completed heating maintenance today. Checked the safety and heating integrity. Checked heating elements. Checked heating operation. Checked amps and cleaned furnace. â€¢The UV light filtration system thatâ€™s in there now isnâ€™t working . Bulbs are broken. Showed family . They will upgrade the filtration system when they are ready and let us know . â€¢The AC coil / Evap coil is very rusty and will eventually cause R22 leaks . â€¢Outside contacter is going bad would highly suggest having it replaced to prevent future issues with the AC system . â€¢Installing Uv light system today . Completed install UV light is working at speck levels .
Heating tune up Jefferson. Completed one system tune up on 7 year old system. Heating is good. Changed filter. System has no back up water safety or surge protection. Home would also benefit from having electro static filter and UV light treatment installed to better filter air and kill any bacteria or viruses in air.
1 upstairs air handler replaced in Jefferson, thank you for your business! Gavin & Eric
Customer would like to replace air handler for upstairs unit. Having team come out tomorrow to replace.
Ac service Jefferson. Completed diagnostic. Found thermostat bad. Forcing fan to stay on. Replaced thermostat. System working properly at this time.
Heating maintenance Jefferson. Completed one system heating maintenance. Found drain line not adequate. Re ran drain line. Installed inline float switch in secondary and drain pan float switch for better water damage prevention. System inside has clean evap coil and clean blower wheel. However inside does have concerning amounts of mold in system. Outdoor unit has good amps on fan and compressor. Capacitor is good and contactor is good. Recommend compressor saver to take load of. Compressor during start up and allow compressor to live longer.
Ac service Jefferson. Completed diagnostic. Found leak in evap coil. Coil needs to be replaced. Ordering tomorrow and will return Thursday to do replacement.
Ac diagnostic in Jefferson, Georgia. Customer says system is not keeping up. Tested system. Found ductwork setup to not be ideal with distribution boxes. Systemâ€™s water safety is code compliant but has not backup. Found mold growing in system. Found dual capacitor to be very weak (40/5 uf). Found system with no hard start kit. Found system with no surge protection. Recommend ductwork renovation, replacement of capacitor, installing a hard start kit, installing an overflow protection switch, installing surge protection and installing up light system to kill mold and purify air. Replaced capacitor for upstairs system. System is operating at this time.
Completed 2 system maintenance. Found both system 1 year old with clean blower wheels and evap coils. Filters are good. Drain lines are clear. System has no secondary water safety device to protect system as well as house from water damage. System would also benefit from having electro static filter installed to better filter air and keep system and home cleaner longer. As well as UV light treatment to kill any and all bacteria viruses allergens in the air that could cause harm to residents. Outdoor systems have good pressures and working electrical components. All amps on motors are good. Capacitor is good. Contactor is clean. Coils are clean. System outside would benefit from having compressor saver and surge protector installed to allow system to live as long as possible.
Installed both inline and drain pan float switch to upstairs system. Tested system and both switches. System cooling at this time.
Thank you! Gavin Mark and Jeff!