Ta explains everything in a way is easy to understand. He shows me everything that I need to know about with the systems.
Seth Delmada arrived on time and was courteous and very professional. We are very happy with our service from Comfort Control.
Completed one system maintenance. Found both systems to have very dirty blowers and the upstairs system is showing signs of possible mold growth. The downstairs system to had a failing run capacitor. Also, the main level system was low on refrigerant. Filled the mail level with refrigerant and both systems are running.
Furnace repair for the downstairs unit. Signed the client up for a new Comfort Club Membership. Performing heating maintenance. Replaced both of the filters. The downstairs system has a warped shaft for the blower motor but it is still working but not balanced. Installed a compressor saver for both systems. The downstairs and upstairs systems are heating normally.
Replaced the thermostat. Signed the customer up for one Comfort Club Membership plan and completed heating maintenance. Left a replacement filter. Tested the mechanical and electrical components and found a weak capacitor. Recommended repairing. Recommended a hard start kit to reduce the load on the compressor. The system is heating at this time.
Replaced defrost board and sensor. Tested system and found to be heating good. Part is under warranty, charged for labor.
Completed heating maint. Filter is clean. Replaced the capacitor and contactor in the condenser. System is getting up in age but working good.
Diagnosed system. Found charge to be good. Error code was stating the pressure switches are cycling, time delay/control board failure, thermostat short cycle. Ran system in both cooling and heating. Talking with the customer. Determined the defrost board is malfunctioning. Order new board and schedule for following Mon 10-12 to replace.
Furnace repair. Checked and found upstairs heat not operating properly. Find auxiliary heat not operating. Find system have broken control wire, repair wire, and system operating at this time. Warranty service call.
Tested the main level system. The heat strips are functional and pulling 20 amps. The refrigerant pressures are good and the line temperature is good. If the customer wants to heat the house better in these low temperatures (20-degree range) they will have to have an electrician pull 6/2 wire with the ground to the unit and we can install a 10 KW heat kit.
Replaced a defrost board and a sensor under full warranty. The system is heating at this time.
Completed 1 system furnace repair and preventative maintenance check. Found heat pump To be running properly. Changed filter. System running at this time.
Furnace repair call. Found downstairs system on a low-pressure lockout. Reset and tested pressures and they are where they need to be. Will return to replace defrost board and sensor under warranty. M/N 14HPX-024-230-18 S/N 1914C64704
Completed 2 system furnace repair and preventative maintenance check. found no issues needing to be repaired at this time. Blower wheels might need cleaning in the next year or two. Systems running at this time.
Completed 1 system maintenance found blower motor capacitor running low. Recommend replacing that part. System running at this time.
2 system heating preventative maintenance and a new Comfort Club Membership. Replaced the filter. Checked the electrical and safety switches. All are okay at this time. Installed a UV light for the main floor system. Installed a compressor saver and added 2 lbs of freon. Both systems are heating normally at this time.