Seth Delmada arrived on time and was courteous and very professional. We are very happy with our service from Comfort Control.
Replaced a defrost board and a sensor under full warranty. The system is heating at this time.
Completed 1 system furnace repair and preventative maintenance check. Found heat pump To be running properly. Changed filter. System running at this time.
Furnace repair call. Found downstairs system on a low-pressure lockout. Reset and tested pressures and they are where they need to be. Will return to replace defrost board and sensor under warranty. M/N 14HPX-024-230-18 S/N 1914C64704
Completed 2 system furnace repair and preventative maintenance check. found no issues needing to be repaired at this time. Blower wheels might need cleaning in the next year or two. Systems running at this time.
Completed 1 system maintenance found blower motor capacitor running low. Recommend replacing that part. System running at this time.
2 system heating preventative maintenance and a new Comfort Club Membership. Replaced the filter. Checked the electrical and safety switches. All are okay at this time. Installed a UV light for the main floor system. Installed a compressor saver and added 2 lbs of freon. Both systems are heating normally at this time.
Completed 1 system furnace repair and preventative maintenance check. Change filter, check safety and operations. Find heatpump/airhandler operating with in manufacturer spec. Suggest surge protection for the heatpump system and suggest inline water protection for the airhandler system in the attic.
Completed 1 system furnace repair and preventative maintenance check. Changed filter. Tested mechanical and electrical components, all in good shape. Recommend surge protection to protect the system from power surges. Recommend apco air purifier to help keep coil clean and to kill bacteria, germs, viruses and volatile organic compounds for improved air quality. The system is heating at this time.
Completed 1 system heatpump repair and preventative maintenance checks complete, found Freon leaks in the evaporator coil. The water heater has a bad pressure valve.
Found dirty filter restricting airflow. Replaced filter. Serviced system and found no safety Switch installed on the drain line. Recommend to prevent overflow of water through the system. Pressures a are good. The system is cooling well at this time.
Complete furnace repair and preventative maintenance check. Find the a/c unit operating normally. Change filter , check operations and safety. Find airhandler have molds growths. Suggest to install apco air purifier to improve air quality and prevent molding. Suggest compressor hard start kit to improve system start up and reduce load.
Renew cci plan and complete cooling pm check. Change filter, check drain and clean ac coil. Find Amana Heatpump system operating normal at this time.
Clogged drain line. Cleared line and system is draining at this time
Water leak due to a clogged filter. Customer will replace the filter. The system is cooling normally at this time.
Found leak in the evaporator coil. Checked with the manufacturer for warranty and found it is not under warranty. Gave multiple options from repairing the leak to replacing the system.