Jordan was very professional and friendly.
Garrett did a great job and worked hard to get us the deal that we could manage.
The technician was amazingly fast arriving and followed through to find the exact problem with the HVAC.
He was very prompt, knowledgeable and friendly. Super helpful
Reece was prompt. Knowledgeable. Kind. Friendly. Very helpful. Awesome.
Jon is very professional and courtesy. He makes sure I understand what he is doing and answers all my questions. He took the time to give me instruction on how to change my electrostatic air filter.
Jon did a great job and explained what he was doing and the related problem.
Complete heating inspection special in Jefferson. Check and find 5 year old Amana Airhandler and Heatpump system operating with in manufacturer spec. System little low on charge but still in manufacturer operating conditions. No concern at this time.
No heat in Jefferson. Homeowner concern with humming outdoor unit. Hum is the sound of the compressor running and is completely normal. System operation normal at this time.
No heat in Jefferson. Check and find 15 year old heatpump and Airhandler ICP system. Find system operating with faulty defrost control board causing system not going to defrost cycle. System will freeze. Find fan motor not size properly. Find drain line not level. Find indoor unit Airhandler operating with bio growth, evaporator coil badly rusted and dirty blower wheel. System operating with no inline water protection in attic. Due to system age and poor conditions, suggest customer to upgrade system.
Warranty Jefferson. Found wires at zone board not connected properly to give power to defrost board. Re did wiring. System is heating and going into defrost board.
Free consultation for heat pump system in Jefferson Georgia 30549
Free consultation for new heat pump Jefferson Georgia
Heatpump not heating in Jefferson, Georgia. Found system with bad compressor, rusty and corroded evaporator coil, weak blower capacitor (7.5uf), dirty blower wheel, weak dual capacitor, and no water safety. Ductwork is not up to todayâ€™s codes because it isnt r8. System runs on r22 refrigerant which has been phased out by the epa. Due to age and condition of system, recommend upgrading system to a more reliable and more efficient system.
Heating maintenance Jefferson. Completed maintenance on 2 1 year old systems. Found both systems heating properly. Both filters changed and working. UV systems both working good. Blowers are clean. Evap coils clean. Static pressure is good on both. Insulation in attic is good. Ductwork is r8. All safety switches working.
No heat Jefferson. Completed diagnostic. Found system low on Freon. Leaking at evaporator coil. System is 12 years old running on r22 Freon. Blower whee is dirty. Capacitor is weak. System has no back up water safety device. Recommend system be replaced due to age, leak, and condition. Customer just wants it filled for now.
Bad defrost board .
Prepaid heating maintenance today in Jefferson Georgia . Checked performance and safety. Checked heating operation and integrity. Checked pressures. Checked amps and heating elements. System is heating at this time . Would recommend equipment have a compressor saver to reduce amps and save energy plus longevity to the equipment.
â€¢Prepaid heating maintenance in Jefferson Georgia. Checked the heating integrity. Checked safety. Checked heating elements and motors . Changed air filter . System is heating at this time . â€¢Biological growth is growing in the air boxes . Would highly recommend a UV light to kill and prevent the growth from spreading . â€¢Would highly recommend the drain line have a overflow water safety device to prevent clogged drain lines/ water damage. â€¢Outside start up contacter is getting pitted and has burn marks would suggest replacing that part to prevent future break downs. â€¢Outside dual start cap is weak and below rating would suggest replacing to prevent future issues. â€¢Will send over recommendations with prices to the email on file .
One system heat maintenance in Jefferson. Arrived on site, changed filter and checked heat kit, checked electrical connections, amp draw and capacitance. Unit is operating normally at this time. Recommended installing air purifier to system to improve indoor air quality and prevent organic growth inside system
Heating maintenance Jefferson. Completed maintenance on new system. Everything installed properly. System is heating properly. Static pressure is good. Everything inside is clean. Changed filter.
Signing family up for the maintenance program in Jefferson Georgia . Going to complete heating maintenance today . Completed heating maintenance today. Checked the safety and heating integrity. Checked heating elements. Checked heating operation. Checked amps and cleaned furnace. â€¢The UV light filtration system thatâ€™s in there now isnâ€™t working . Bulbs are broken. Showed family . They will upgrade the filtration system when they are ready and let us know . â€¢The AC coil / Evap coil is very rusty and will eventually cause R22 leaks . â€¢Outside contacter is going bad would highly suggest having it replaced to prevent future issues with the AC system . â€¢Installing Uv light system today . Completed install UV light is working at speck levels .