Vu Tran not only performs the required services, but he tightened screws to the door from hall to downstairs. He is the one who saw the need!
Always a pleasure to have Vu over!
Vu was great! Very professional and informative.
Very effective and helpful
I always request Vu for each of my service calls! What a great & knowledgeable guy
Comfort Control, great as always
Complete 1 system a/c repair and preventative maintenance check.Did not change filter, check safety and operations. Find 8-year-old Amana system operating within manufacturer spec. No concern at this time. Suggest air purifier system and surge protection for system.
Sign 2 Comfort club memberships. Complete 2 system a/c repair and preventative maintenance check. Change both filter, check drain and operations. Find both cooling system operating within manufacturer spec. No concern at this time. Suggest inline water protection for system in attic, suggest hard start kit for both cooling system and air purifier system to help improve air quality and prevent molding.
Complete 1 system a/c repair and preventative maintenance check. Replace warranty condenser fan motor under parts and labor warranty. No charge to customer. Test and find system operating within manufacturer spec. No concern at this time. Suggest hard start kit and suggest surge protection for outdoor unit. Customers have whole-house surge protection.
Complete 1 system a/c repair and preventative maintenance check. Change filter, check drain and operations. Find condenser fan motor fail and ac unit shut off on safety. Need to order Lennox condenser fan motor under manufacturer warranty and under labor warranty. System off at this time. Need to schedule for Friday 22, to replace motor.
Client stated condenser was louder than normal. Came to home condensing fan motor is wearing. Client has been made aware that the condensing fan motor can seize and stop working. Client denied repair of condensing fan motor. System is operating and cooling at this time.
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at email@example.com or call us at (770) 932-5012.
No heat. Check and find crawlspace pump connected with furnace tripping breaker. Remove cord from furnace outlet and power not tripping. Customer need to get Crawlspace pump check. Complete 2 cooling pm check. Change filter and check operations. Find main system low voltage control system damage, repair wire for customer. Find ac system operating poorly and burnt wire. Both ac system 27 year old, customer need consultation visit. System operating at this time but in poor conditions and not reliable.
Complete system tune up inspection. Find system tstat fail, replace tstat and rewire system for proper operations. Replace filter with Aprilaire 810. Check and find system duct very dirty and blower assembly dirty and need cleaning. Give estimate for duct cleaning with fogger and blower assembly cleaning. Find ac system operating with low charge and capacitor not mounted, Remount Capacitor. Find system missing starter kit, and condenser coil dirty, give customer estimate to repair system. Customer will look over estimate. System operating at this time.
Renew 2 Comfort Club membership. Complete 2 system a/c repair and preventative maintenance check. Change filter, check drain and clean ac coil. Customer already replace Apco UV bulb. Find upstairs condenser motor show sign of ware. Need to keep check.
Complete 2 system a/c repair and preventative maintenance check. Change both filter, check drain, safety and operations. Find upstairs ac system operating with out stater kit and fan motor worn and sticking. Need to keep check. Find downstairs 3 year old system operating with in manufacturer spec but missing stater kit. Both disconnect box worn and breaker not size properly for equipment.
Complete 1 system a/c repair and preventative maintenance check. Complete ac inspection for downstairs system. Recharge system to manufacturer spec and replace filter 16x25x5.
Complete tune up inspection special. Change filter, repair minor damage power switch for furnace. System operating at this time. Find missing drain pan and missing water protection under furnace . Filter cover missing. Find duct system very dirty, blower assembly dirty. Find ac unit operating at this time, system operating with low charge, coil dirty, capacitor week on fan terminal. Find disconnect arching and worn. System need duct cleaning, need to pull and clean blower assembly for proper airflow. Need to install drain pan and water protection. Need to recharge system to manufacturer spec, need to replace weak capacitor and install hard start kit for proper start up, need Chemical clean AC coi and need to replace disconnect box for safety. Give customer estimate.
Completed 1 system air conditioning repair and preventative maintenance check. Checked all of the mechanical and electrical components of the system and found system with no power. Customer needs to call electrician to check the breaker and power supply to the furnace. Left system as is until electrician can take a look at it.
Complete 2 cooling maintenance checks. Did not change filter upstairs filter and change the downstairs filter. Find both ac system drain missing in-line water protection and suggest to install for water safety. Find both ac units operating with manufacturer spec. Suggest a hard start kit to help the system start-up and reduce load. Suggest upgrading both old breaker boxes for both outdoor units.
Complete 1 system a/c repair and preventative maintenance check. Complete cooling pm check. Install stage 1 pureAireX filtration system. Replace apco uv bulb, install hard start kit and new thermostat Aprilaire8466 and recharge system to manufacturer spec. System cooling at this time. Increase pureAireX stage 3 to 50% opening.