Vu is great! Second time with him as our tech. He’s polite, punctual & detailed.
Garrett did a very good walk through and explained everything and answered all my questions in a very professional manner
why no early appointment discounts as past years....loyal customer...
Provided great service and excellent detail summary of the status of the two units.
Outstanding service for several years.. highly recommended...
Always excellent work and very personable. Explains everything so I understand and is on time.
We would recommend you and Ta to anyone who needed temperature control. Love those calls to let us know the time!
Complete 1 system a/c repair and preventative maintenance check. Install water protection for the system in the attic.
Complete 2 system a/c repair and preventative maintenance check. Change both filters, check the drains and clean a/c coils. Find upstairs system operating with a low charge, missing water protection for both systems in the attic. Find system missing hard start kit. Recharge system to manufacturer spec. Find downstairs system 2 years old, operating within manufacturer but missing hard start kit. Find both outdoor breakers at 60amp and should be 30amp rated. Both system gas line not up to code. Give customer estimate to install safety, and get the system up to code.
Complete 1 system a/c repair and preventative maintenance check. Find cooling system operating within manufacturer spec. Find heating system operating with manufacturer spec. The system is heating and cooling properly at this time. Change filter and check system safety.
Complete 1 system a/c repair and preventative maintenance check. Changed filter. Cleared drain line. Chemically washed condenser coil. Tested mechanical and electrical components. Found breakers to be oversized for the condenser. Found early signs of mold in the system, recommend platinum IQ to kill mold, bacteria, germs, and viruses for improved air quality. Recommend hard start kit to reduce the load on the compressor. The system is cooling at this time.
Complete 1 system a/c repair and preventative maintenance check. Found system almost completely empty of Freon, and condenser coil very dirty, and pitted contractor. The system is 23 years old, recommended replacement. The client will call us after making a decision
fix deferred revenue for accounting
Complete 2 system a/c repair and preventative maintenance check. Recharge both systems with R22. Change filter, check the drain and clean ac coil. Both system operating at this time.
Sign up 2 cci plan and complete 2 cooling pm check. Change both filter. Clean ac coil, check drain and system operations. Find both system operating with with worn compressor and high amp. Fan motor worn and running hot. Both system evaporator coil rusted. System charge are good conditions.
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at firstname.lastname@example.org or call us at (770) 932-5012.
Renew Comfort Club membership. Complete 1 system a/c repair and preventative maintenance check. Check operations, change the filter and clean ac coil. Heatpump system operating within manufacturer spec. Filter size 20x25x5
1 system A/C renewal of Comfort Club Membership. Replaced filter and clean condenser coil. Found system with burnt/pitted main switch replaced the switch. The system is cooling normally.
Completed 2 system maintenance found both units low on refrigerant with low reading run capacitors as well as dirty blower wheels for each. Both units have no secondary water safety device. Also, the downstairs A/C has a low reading capacitor. The customer would like Garrett to come out and talk about options for replacing.
Renew 2 Comfort Club Membership plans and complete 2 cooling preventative maintenance check. Change both filters. Replace 2 capacitors and install 2 hard start kit for both Lennox system. System operating at this time. Need to keep a check on fan motor for the upstairs unit. Motor making minor noise.
Renew cci plan and complete cooling pm check. Change 20x25x1 filter, check drain, and system operation. Find system operating within manufacturer spec. Suggest compressor hard start kit to improve start up and reduce load.