complete 2 system furnace repair and preventative maintenance check. Renew 2 comfort club memberships. Change both filter , check safety and operations. Find upstairs heating system operating with in manufacturer spec. Poor water safety setup, and flue pipe not up to code. Find main system heating not operating inducer motor lock up from water calcium build up. Clean inducer assembly. Complete combustion calibration service and replace worn ignition. System operating at this time.