New guy for me but he was nice and he did his work and was very professional
The Comfort Control Technician was knowledgeable and thorough performing the service on our heating system. We were pleased with the services rendered.
I am so impressed with Comfort Control!! John was here to fix my system within hours and I was not charged the typical “weekend” or “after hours” rate. The service was very affordable!! I am so thankful for you!!!
Vu is the most knowledgeable HVAC technician, he was thorough and precise with checking every part of our systems and showing us detailed photographs so we could see and understand what was going on. ***** 5 star recommendation for Vu and Comfort Control!
Vu is an excellent technician. He performed an in depth diagnosis on the heating and air systems and performed the necessary maintenance and repairs. He has maintained our system for many years and we have always received great service.
First of all, Very friendly and informative. Answered questions and was informative as well on overall heating and air.
Great service. Super attention to detail!
Hvac tune up in Loganville, Georgia. Two systems. Changed filters. Found upstairs system not coming on due to high voltage wiring going into furnace burnt. Both nest thermostats did not have common wire hooked up. Hooked up both common wires to both thermostats and control boards and repaired high voltage wiring going into upstairs furnace. Tested mechanical and electrical components. Found downstairs ignitor to be worn. Found downstairs flame sensor to be bad and intermittently failing. Found downstairs blower wheel to be dirty. Found no water safety on either system. Found evaporator coils to be rusty, corroded and likely to leak refrigerant. Found upstairs ignitor to be worn. Found upstairs blower capacitor to be extremely weak, reading a measurement of 2 microfarads when it is rated for 10, could fail at any time. Found downstairs disconnect box for condenser to be broken with melted plug. Downstairs Ac is not functioning due to this. Found downstairs main electrical switch with ba
Two system tune up in Loganville. Arrived on site, checked filters and cleared barometric ports, checked ignition systems, electrical connections, amp draw and capacitance. Found older unit that services the left side of house has no aux drain pan and no water safty. Recommended installing wet switch to sense any moisture in the event the unit were to fail. Recommend replacing equipment in near future due to age as well as condition of equipment. The newer system that services the right side of house is functioning on a weak blower motor capacitor. I also recommend installing a secondary water safty switch to protect the electrical systems as well as serve as a backup for the pan switch. Static pressure in both units is fantastic except across the filters, recommend installing electro-static filter to help with air flow as well as helping to better clean air as it enters the system. Also, I recommend installing surge protection to both of the indoor units to protect electrical systems.
No heat in Loganville. Check and find downstairs gas furnace not operating and lock out on safety. Find pressure not operating properly. Replace e pressure sensor and system operating at this time. Check and find flame sensor weak, ignition worn and blower capacitor bad. Find system have not water protection, flue pipe not code. Customer need consultation visit for downstairs 15 year old system. Long-term customer, waive service fee.
Service call in loganville. Replace full part/labor warranty gas valve for Amana gas furnace in attic. Check and find new valve operating with in manufacturer spec. Find furnace operating within manufacturer spec. Check for gas leak and did not detect gas leaking at furnace. System operating at this time.
No heat in loganville. Check and find gas furnace gas valve fail. Need to order from manufacturer under part warranty. Give customer estimate to repair. Need to check with labor warranty for customer. System off at this time.
One system heating tune up in Loganville. Arrived on site, changed aprilair 610 filter and cleared barometric ports, checked ignition systems, electrical connections, amp draw and capacitance. Recommended installing secondary water safty switch and surge protection to unit to protect electrical systems. Unit is operating normally at this time
No heat Logan Iâ€™ll. Completed diagnostic on 21 year old system. Fuse was blown. Replaced fused. System came on and ran on heat for 10 min. System heating properly. System is 21 years old with dirty blower wheel and no water safety. Air flow is restricted due to inefficient duct work. Evap coil is leaking r22. System needs to be replaced.
All code upgrades and repair were completed in Grayson/
2 system heating and cooling inspection in Loganville / both systems are working / water safety issues with both systems/ and bad capacitor on upstairs system
Complete 3 heating maintenance in loganville. Find upstairs 4 year old Lennox gas furnace operating with in manufacturer spec. Find R6 ductwork and missing in-line water protection in attic. Find main level carrier 6 year old gas furnace operating with in manufacturer. System flue pipe not code due to undersize and missing water protection. Find basement 22 year old Armstrong gas furnace not operating properly due to worn ignition. Find furnace control board overheating, worn inducer motor and motor. System missing water protection, flue pipe not code and gas line not code. Customer only want to repair furnace for now. Replace furnace ignition. System operating at this time. Find bio growth on upstairs system, suggest pureAireX air purifier system. Give customer estimates.
One system heat maintenance in Loganville. Arrived on site, checked filter and cleared barometric port. Checked ignition systems, electrical connections, amp draw and capacitance. Found system without water safty, recommend installing in addition to surge protector to protect electrical systems. Also recommend pulling and cleaning blower motor assembly to keep fan properly balanced. Recommended installing uv system to improve air quality inside house. Unit is operating within manufacture spec at this time
â€¢Completed a 2 system heating maintenance in Loganville Georgia. Prepaid visit today . Changed air filters. Checked the heating operation. Checked the integrity of the heating elements. â€¢Recommend having the draft B vent removed and cleaned . Took a video of all the rust and debris. This will eventually clog up the inducer draft motor. â€¢Today I cleaned out the B vent and the inducer housing port . System is heating at this time . â€¢Basement system is heating at this time .
Arrived on site, found a popped fuse in furnace, replaced and tested system furnace came right on no issues. Replaced capacitor (per-Tom/Phill) tested system, unit is operating normally at this time.
4 system heating maintenance/no cool in Loganville arrived on site. Checked filter and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Found outdoor unit for master bedroom was completely dead on fan side, recommend replacement. All systems are heating normally at this time.
No cool in loganville. Check and find system freezing up due to low charge. Find 24 year old Trane air conditioner unit. Find system have small leak at evaporator coil in crawlspace. Find gas furnace operating with high co level. Sign 1 cci plan and complete heating pm check. Change filter. Recharge ac unit with R22 and replace APCO UV Bulb. Customer want to wait on combustion calibration service to help reduce co levels.