Customer complained of poor dehumidification, poor airflow, and mold. Installed breathe easy blower ionizer, growth inhibitor, and bacteria and mold eliminator. Installed two forms of water safety. Redid drain line, installed condensate pump both new Beckett tubing. Removed, cleaned, and reinstalled evaporater coil. Pulled and cleaned blower wheel assembly. Found bad capacitor, replaced capacitor and installed hard start kit. Signed customer up for one system maintenance plan and performed maintenance. Cleaned washable filter. Chemically washed condenser coil. System is cooling normal at this time.