Water heater fault in Lula. Arrived on site, found 2002 water heater control board completely fried. Due to age of system recommend replacing
Completed 2 system maintenance. Upstairs system is 4 years old with clean blower clogged drain line. Clean evap coil and very dirty filter in one of the 3 returns. Other returns had no filter and no filter at system. Took small filter out of return and added filter at the system to filtrate all 3 returns. Cleared drain line. System has no water safety. Added inline float switch. System would benefit from having UV light installed to kill and bacteria viruses or allergens that could cause harm to reseidents. Downstairs system is 6 years old with clean blower and coil. Has clogged drain line and no filter. Added filter at system. Cleared drain line system also has no water safety. Installed inline float switch. System would also benefit from UV light installed. Outdoor unit has good pressures and working electrical components. Systems would benefit from having compressor savers installed to take load off compressor during start up and allow compressor to live longer.
Complete 1 system furnace repair and preventative maintenance check. Found fan blade snapped off. Replaced blade checked pressures. Pressures are good. The system is 10 years old compressor running good nothing overheating. Capacity still within manufacturing spec. The customer will talk with the father(landlord) about the maintenance plan.
Found blower motor not coming on due to bad blower motor controller, bad motor and bad relay. Due to age and condition of system, recommend upgrading to more reliable, more efficient system. Will send Garrett back out for free consultation.