Found system with burnt wiring in furnace and damaged flexible gas line. Repaired wiring. Replaced flex gas line. Signed customer up for one system maintenance plan and performed cooling maintenance. Chemically washed condenser coil. Recommend surge protection to protect equipment from power surges. System is cooling at this time.
Complete 1 system furnace repair and preventative maintenance check. found gas valve flickering 2-3 times before staying on. Need to replace the valve. Going to tri-state tomorrow to get the part and return tomorrow to replace it.
Complete 1 system furnace repair and preventative maintenance check. Pressure switch was stuck open due to water getting inside. Cleaned out switch. System heating properly.
Complete 1 system a/c repair and preventative maintenance check. Found duct had come off plenum. Reattached duct. Ducts are old and drenched. Need to be replaced and need to add a UV air purifier to the system.
Broken a/c repair call. Checked and found the system frozen due to low charge and leaking. The customer had to add several charges last year. Due to the system's age, poor conditions, and leaking charge I recommend the customer upgrades the system and does not repair. Customer need estimates. The office will schedule asap.