Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at email@example.com or call us at (770) 932-5012.
Found the system not heating. Cycled the power and cycled the gas valve. The system is heating okay. It is a very old package unit. Setting up a time for the Comfort Advisor to come out and give options to upgrade the system.
Completed 7 system furnace repair and preventative maintenance check. Find Main house with 3 HP/AH system. -Upstairs system operating with in manufacturer spec. Filter still good. -Main system operating with in manufacturer spec. Filter still good. -Basement system 17 year old operating with stress compressor and high power usage, low charge and damage wire due to rats chewing on wire. Remove dead rat and repair wire for the customer. Suggest repair basement system. Give customer estimate. Find Guess house with 4 HP/AH system. -Upstairs new system operating normally within manufacturer spec. Filter still good. -Upstairs system for bedroom 17 years old molded and dirty. Find system evaporator coil badly rusted. Missing inline water protection for the system in the attic. Motor and compressor in poor conditions due to age and ware on parts. Low on charge. Give customer estimate to repair system, but suggest to upgrade system due to age.
Replace upstair new heatpump system coresense. Check and system operating at this time.
No cool again on new install. Test and find heatpump system not operating. Test and heatpump system core sense faulty and need to replace. Need to order new core sensor and come back to replace under warranty. Bypass core sensor and system operating at this time.
A/c repair call for a new system installed in the upstairs. Checked and found the system on lockout for safety. Reset and tested system. Found loose txv bulb causing the unit to not meter properly after long run time due to manufacture not mounting txv bulb. The system is operating at this time. Full warranty. Install compressor start kit to improve start up.
Found the new system off through the diagnostic box in the condenser. Reset system and told the customer if it happens again it will be bypassed. Checked system and it's cooling well. No other issues found.
System was running upon arrival. Checked amps and pressures. Suspect the circuit board failing in condenser. Customer recycled the high voltage and the system came back on.
Found system out of Freon. Recommended upgrading system. Will call cust back tomorrow with availability on install time. Customer would like before Thursday due to guests arriving.
Bring a sheet of duct board, programmable thermostat, horizontal drain pan, two forms of water safety, will need to move existing Apco to the new air handler.
Bad board caused a fault in relays as well causing heat strips to stay energized and fan on continuously. The system is old, full of mold and runs on refrigerant being phased out by the EPA in 2020. Recommend replacing the system. The model number of current carrier air handler is NFCX4800C1 and serial is L995162224. Customer will think over options and call us back
Replacing board and 2 sequencers.air handler working properly. New board and heat strips installed. During testing noticed outdoor unit not running. Outdoor heat pump off on low pressure due to completely empty of refrigerant. Fins of outdoor coil corroded and leaking. System will not hold a charge due to the size of the leak. System is r-22 refrigerant and will be unavailable Jan 2020 due to EPA regulations. If heat pump is replaced the evaporator coil upstairs will also have to be replaced do to the pressure difference and the inability to flush r-22 out of the coil. All new systems use 410a refrigerant. The two options to fix the situation are to replace the heat pump and the upstairs coil or replace the entire system which is the recommended action because of the warranty and efficiency difference. Heat is operating solely on emergency heat and the outdoor unit will remain inoperable until it is replaced.
Heating Repair: Guest house upstairs system heat was staying on. Diagnosed problem with control board and high voltage strip heat sequencers. Gave 3 options to replace bad parts in existing air handler or the entire system. Service call price will be dropped with an installation