Always very thorough, knowledgeable and courteous would recommend highly
Reece was professional, courteous and a Star Wars geek like me.
Had a large install of new ductwork and insulation. Guys were great, super nice, and accommodating. Very pleased.
Love having a company that I can trust. James went through all our systems, made a few minor repairs, and gave us some suggestions. All completed in just a few hours. Awesome company.
Did a great job of going over everything and giving the system a thorough check.
Great job by our technician, Mark. Kept in touch about arrival time. He was prompt, professional and efficient. He made the necessary repair, checked everything and made sure he had answered all our questions.
Thou I did not appreciate the nasty notice saying my maintenance agreement had expired Voo was polite, professional, efficient and personable.
I’ve always requested Vu when scheduling my yearly a/c and furnace maint because he’s professional, honest, skilled at what he does and very friendly. I wish there were more appliance techs like him.
Complete 2 system tune up inspection special in Norcross. Find both 4 year old Amana system operating with in manufacturer spec. Replace filter customer provided. Check safety and operations. No concern on equipment. Suggest air purifier system for upstairs, suggest surge protection for both unit and suggest hard start kit to help improve start up and reduce load.
Complete 16 heating maintenance in Norcross. Change filter, check safety and operations. Unit #1 capacitor bad 10/15 uf rated Weak flame sensor Need combustion calibration No water protection Unit #2 bad capacitor and missing drain pan float switch for water protection Unit #3 capacitor bad 17.3/20 uf rated Weak flame sensor No inline water protection Unit# missing in-line water protection Unit#5 dirty blower assembly, weak capacitor and rusted Evaporator coil, and missing in-line water protection Unit#6 No water protection Unit# 7 Gas line not code No inline water protection Unit#8 Gas line not code No inline water protection Unit# 9 Gas line not code No water safety Unit# 10 No inline water protection Gas line not code Unit#11 No inline water protection al Gas line not code Unit#12 Bad thermalcouple Stress and overheated heat exchanger Fail unit and not safe to operate Need to replace 26 year old system Unit#13 Fail unit not safe to operate, flame rollout, in
Service call in Norcross. Complete tune up inspection special. Replace dirty filter, check safety and operations. Find poor duct system in attic and only R6 rated and need to be R-8 to meet code. Find daughter bedroom 6â€ duct run in correctly and reducing air flow. Adjust for customer to increase air flow. Find 10 year old Trane gas furnace operating with weak flame sensor and combustion calibration off. Suggest repair and give customer estimate to for duct system.
No heat in Norcross. Arrived on site, found outdoor unit freezing up due to low refrigerant pressure. Found leak in evaporator coil in 09 air handler for basement unit during spring visit. At this time I highly recommend replacing equipment
Complete 2 heating maintenance in Norcross. Find 2 10 year old Goodman gas furnace operating. Change both media filter customer provided. Check safety and operations. Find upstairs gas furnace operating with in manufacturer spec. Find inducer assembly motor starting to ware and motor making minor noise. Need to keep check. Reduce heating fan speed to help reduce noise for bedroom. Find downstairs furnace operating with in manufacturer spec. No concern at this time. Suggest in-line water protection for both system, suggest surge protection and air purifier system.
Complete heating maintenance in Norcross. Check safety and operations. Find 17 year old Trane gas furnace operating with worn flame sensor and worn ignition. Furnace under fire. Customer want to keep a eye on the system for now. System operating at this time
Furnace maintenance in Norcross, Georgia. Two systems. Did not change filters. Tested mechanical and electrical components, all in good shape. Recommend overflow protection switches to serve as a backup to primary water safety and to help prevent water damage to furnaces. Recommend surge protection to protect equipment from power surges. Systems are heating at this time.
Complete heating maintenance on 2 year old Rheem gas furnace in Norcross. Change filter, check safety and operations. Find gas furnace operating with in manufacturer spec. No concern on furnace. Find customer have 13 year old GE gas hot water heater leaking water. Reduce temperature for hot water to help reduce pressure and reduce water leakage. Due to hot water heater age, suggest to upgrade hot water heater.
Renew comfort control plan and complete heating maintenance in Norcross. Change filter, check safety and operations. Find 7 year old heating gas furnace operating with in manufacturer spec. Little high in static pressure.
Complete 3 heating maintenance in Norcross. Find 3 Amana gas furnace operating with in manufacturer. Complete combustion calibration service for the need furnace. Change all filter, check safety and operations. Replace both apco UVbulb. All 3 operating at this time.
Complete heating maintenance in Norcross. Find 10 year old Lennox gas furnace. Check safety, change and operations. Find Lennox gas furnace operating with weak capacitor, weak flame sensor and worn ignition. Replace capacitor, replace flame sensor and ignition. System operating at this time. Flue pipe not up to to code and gas line not up to code.
Complete heating maintenance in Norcross. Check and find 7 year old Lennox gas furnace operating with in manufacturer. Change filter, check safety and operation. Customer want to wait to spring to replace apco UV bulb.
Complete heating maintenance in Norcross. Change filter, check safety and operations. Find Amana gas furnace operating with in manufacturer spec. No concern for furnace at this time.
â€¢Completed a 7 system heating maintenance in Norcross Georgia. Changed air filters . Checked the heating operation and safety. Checked heating elements/ integrity. Today was the prepaid maintenance visit. â€¢Lennox system labeled #7 has been causing water issues. Looking over that issue today . Found the condensation pump has failed and wasnâ€™t working consistently. Replaced pump and put new pee trap on the drain and a coupling . System is heating normal at this time . â€¢Hanging units in the workshop would highly recommend inline water safety switches to prevent water damage on the equipment and work equipment. Blower start cap is weak on the blower motors would highly recommend replacing that electrical part to prevent future issues. Both hanging units are heating normal at this time. â€¢Unit #6 . Has a clogged drain line that has alarmed the water safety device going to have to flush and clean the drain line . Flushing and cleaning out the drain line today . Completed and n