Did a great job of going over everything and giving the system a thorough check.
Great job by our technician, Mark. Kept in touch about arrival time. He was prompt, professional and efficient. He made the necessary repair, checked everything and made sure he had answered all our questions.
Thou I did not appreciate the nasty notice saying my maintenance agreement had expired Voo was polite, professional, efficient and personable.
I’ve always requested Vu when scheduling my yearly a/c and furnace maint because he’s professional, honest, skilled at what he does and very friendly. I wish there were more appliance techs like him.
Always a pleasant experience having Comfort Control our for routine service on our heating and air units.
Fast & efficient
No cool on mini split system for server room in Norcross. Check and find system low on charge, customer know system have small leaks and only want to recharge for today visit. Recharge with 2 lbs of R410. System operating at this time.
No cool. Found condenser coil dirty and system low on r410a. Customer wants to just recharge system for now. Cleaned condenser coil and recharged system. System is cooling at this t8me.
Ac service in Norcross. Dropped off warranty ecobee
Customer called for Diakin quote on basement air conditioning and furnace, bad application quoted ductless mini split, she has other quote, will talk to husband and make a decision
2 stage full system replacement in Norcross. 1 6inch duct installation in office. Customers are happy and cooling! Thank you for your business! Gavin and Mark
No cool upstairs system. Check and find upstairs system not cooling due to low charge and freezing up evaporator coil in attic. Give customer estimate to replace evaporator coil. Suggest to upgrade 12 year old system.
No hot water. Check and find 18 year old hot pilot fail, re-light pilot and system working, due to worn parts and age of system will fail again. Hot water tank worn and rusted, need to replace. Find 18 year old cooling system with rusted evaporator coil, worn pitted contactor, missing hard start kit and missing service valve cap. Find coil very dirty and need cleaning. Replace 16x25x1 filter for customer and add 2 cap for customer. System operating at this time.
Comertial unit with no access, unable to service unit most likely a refrigerant leak.
August 8th furnace control board fan relay failed. Returned August 11th to replace furnace control board. Part has warranty, labor is not covered. Client prepaid August 8th for repairs. System operating as intended at this time fan turning off and on even calling.
On site found furnace fan operating with no call for fan or cooling. Recommend to replace control board for bad fan relay.
No cool break room system. Thermostat wasnâ€™t well connected to base and had no common wire. Wired it to have a common wire and system is cooling at this time. Found unit 1 system with no r22, major leak has been sprung. Compressor is in very bad shape, system needs replacement.
Complete tune up special for Lennox system. Change filter, check drain and clean ac coil. Find 6 year old Lennox system operating with in manufacturer spec. Compressor making noise at start up and heavy load. Install hard start kit to help improve start up. Find upstairs older system missing filter, system very dirty and water in drain pan. Drain line clogged. Due to system age, conditions of system and dirty system, suggest to upgrade and not repair.
Completed evap coil replacement and added inline float switch to system.
Completed diagnostic. Found system frozen and leaking out of evap coil. Need to replace coil. System also has no water safety. Needs inline float switch to protect furnace and home from water damage. Returning Monday to do both repairs and do first maintenance. Signed customer up on maintenance plan.