Jon served my house in Buford. He is not just a service guy but more like a little brother I see twice a year. Now in Oakwood he has been here twice. I never have to worry about having a stranger in my house. Because he is so personal. We have over the years gotten to know each other, very important to me. You don't have to show me what he looks like, I know. Trust is also important to me Comfort Control has it. And they send me a tech that I know and trust is a big deal. Don't blow wind up my skirt to sell something. If he says it needs to be fixed or replaced I respect that and so confident I get it done..
Have always had excellent service with Comfort Control! Thanks Jon!
I have never in all the years I have used this company, had ant reason complain.
Casey explained everything we needed to have done, how the membership works, and how our systems are doing now.
Oakwood new install
Free consultation for new heat pump oakwood georgia 30566
Heating tune up in Oakwood. Tested operation of 1 system. Discovered supply plenum completely disconnected and damaged, duct and system has heavy amounts of organic growth, blower wheel is dirty and needs to be cleaned to provide proper airflow and balance to preserve life of blower motor, compressor would really benefit from compressor saver hard start kit to reduce stress on compressor and reduce energy consumption on start up. The drain line runs uphill and has no water safety to help prevent flooding. System low on charge with leak detected at evaporator coil. System needs ultraviolet light system to combat organic and viral growth in system and throughout the home. Systems needs repairs to properly heat and cool the home. Duct cleaning is also recommended. Due to high repair cost and age of equipment replacement is HIGHLY recommended.
Furnace not heating in Oakwood, Georgia. Found failed igniter and thermostat. Replaced both and system is heating at this time. Found blower wheel to be dirty and no water safety present in system. System has high static pressure.
Warranty call in oakwood. Arrived on site, customer complaint of loud hissing noise coming from the outdoor unit occasionally. Determined cause to be a defrost cycle. Tested components and pressures, found no issues present at this time.
Repair Oakwood. Completed replacement of inducer motor. System came on. Heating properly.
Heatpump not heating in Oakwood, Georgia. Found one pole of breaker for air handler to be broken. Replaced breaker and restored power to the unit. Found unit to be low on refrigerant and shutting off on low pressure. Due to cost of repair, recommend upgrading system to a more reliable and more efficient system.
No heat Oakwood. Completed diagnostic. Found inducer motor has failed. Need to be replaced. Need to order part and return to replace.
Gas leak in Oakwood Georgia. Found gas line with a leak took videos and pictures also system has been red tagged by the gas company. Flex hose is running into the furnace which is a safety issue. Neither the furnace or water heater has a sediment trap . Need to hard pipe the gas line going into the furnace and water heater and add sediment traps to both . Today weâ€™re fixing the gas line . Put a new shut off valve on the gas line . Added two sediment traps . Installed hard pipe in the furnace. Fixed gas line . System is now operating and not leaking gas into the home .
Inspection oakwood. Completed fill up of minisplit system. System has no refrigerant in it. Leaked all the way out. Filled it to manufacture spec. System heating at this time. System needs to be replaced due to leak b
Heat maintenance oakwood. Completed maintenance found both units heating properly. Upstairs has good UV light and zoning is working. Safety switches work. Changed filter. Downstairs has no UV light but heating good. Safety switches work and changed filter. Installed UV light to system downstairs. Both heating at this time.
Heating maintenance Oakwood. Completed maintenance on 11 year old system. System is heating good. Emergency strips are good and clean. Blower is a little dirty. If worsens will need to pull and clean to avoid loss of air flow. Safety switches working. Evap coil still has corrosion but no signs of leaks. Changed filter. System heating at this time.
Heating maintenance Oakwood. Completed 2 system maintenance on 2 5 year old systems. Both furnaces heating properly. Upstairs has gas line not ran properly. Also UV light needs to be replaced. Downstairs needs UV light to take care of whole house. Relaced UV light and re ran gas line to make proper use of sediment trap.
Heating maintenance Oakwood. Completed one system heating maintenance on new system. Found furnace heating good. Everything installed properly. All safety switches work. Replaced filter. Everything inside clean. Home would benefit from having electro static filter and UV light treatment installed to better filter air and kill any bacteria or viruses in air and take care of any harmful chemicals in air.
Heating maintenance Oakwood. Completed one system maintenance on 3 year old air handler. Found system heating properly everything clean. UV light is good until spring. Changed filter. Missing secondary water safety device