He needs a raise. Good employee
These guys are great. One of them even took off his shoes before entering our house and not because we asked him. He did it on his own. I know it was probably hard to put them on take them off. I really like these guys. I would definitely use them again. Great job guys.
Keep doing what you doing
Completed a system tune up found 19 year old system with good pressures and good capacitor and contactor. System does not have a hard start kit or any surge protection installed recommend hard start kit to prolong life of compressor by taking away a lot of power from compressor during initial start up. Also recommend surge protection to prevent all components in condenser from possibly over heating or blowing all together during a power surge. Also recommend apco UV light to kill and prevent any bacteria or growth from accumulating in house or ductwork. This will also clean and purify air and any unwanted odors in house. System is cooling.
A/C repair for a mini split. Check and find system low charge. Leaks but did not detect the leak. Did detect very small amount at the mini-split head but not sure if is it a leak. Recharge system and add a sealer to help with leaks. Tighten valve connection and cap. System operating at this time.
Complete 2 system a/c repair and preventative maintenance check. Washed condensers. Replaced filters. Added inline safety switch to Furnace in Attic. Recommend start kit for downstairs condenser and adding an additional APCO to downstairs. The customer could only do the inline switch for now. Renewed Comfort Club membership.
Completed install of Apco UV light
Installed uv bulb
Completed 2 system maintenance found both run capacitor low and signs of mold in upstairs unit as well as no secondary water safety switch on both inside units. Outside units are cleaned and pressures are good. Recommend hard start kit to downstairs system and surge protector for both. Changed filters. Systems running at this time.
Cooling preventative maintenance. Added surge protection to the outdoor unit. Need to return to change out UV bulb as I am out of stock. System operation normal at this time
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at firstname.lastname@example.org or call us at (770) 932-5012.
Dehumidifier was leaking water due to clogged ptrap. Cleaned trap, cleaned pump and added chlorine tablets to condensate pump. Went ahead and did cooling maintenance and found weak capacitor in condenser.replaced capacitor. Changed filter customer provided. Chemically washed condenser coil. System is cooling at this time.
Completed one system maintenance found unit to be running on low pressure recommended leak seal and add refrigerant since we have added some in the past. Completed repair. Filteris good coil is clean. Bloweris clean. System running at this time
Completed one system furnace repair and preventative maintenance check. Thermostat wire coming from wall has 2 green wires. Crossed the 2 wires which caused the heat to run continuously. Switched back and checked all functions.
Completed one system furnace repair and preventative maintenance check. Replaced circuit board and thermostat. Checked heating and cooling. Both cycles work well.
Found a shorted circuit board. Ordered a board from the manufacturer. The board is scheduled to come in tomorrow. Signed the customer on the Comfort Club Membership. Also, I will be replacing the thermostat on the same day.
Completed 1 system furnace repair and preventative maintenance check. Found the unit to be old but still running. Blower whee was very dirty and needs to be cleaned. System has no water safety and needs to have an inline float switch installed. Flame sensor is very white and brittle looking and needs to be replaced. Customer declined all repairs for now. Filter looks good for now. System running at this time.
Customer wanted to know why outside unit kept coming on. Explained to customer it is a heat pump that is used for both heating and cooling and that everything is working the it should be. System running at this time.