Completed diagnostic on 3 year commercial unit. Thermostat not wired correctly to activate reversing valve. Re wired. System also was charge way over the limit of refrigerant that it calls for. Was locking out on high pressure. Retrieved refrigerant to get pressures good. 25 degree superheat and 9 degree subcool. System cooling at this time.