1 system A/C renewal. Replaced filter, cleared drain and clean condenser coil. The system is cooling normally
1 system furnace repair and preventative maintenance check Replaced filter, checked electrical and safety switches all ok at this time. Suggest adding Apco UV light for bacteria and mold prevention. Replaced blower starter, tested and the system is heating normally.
1 system cooling early bird special. Replaced filter. Found mold and rust inside air handler. Found weak blower motor controller and burnt/ pitted main switch. Owner wants to wait. System is cooling at this time.
Zone 3. 1 system heating prepaid pm. Left filter for owner, checked electrical and safety switches all ok at this time. Replaced voltage absorption for heatpump. Needs uv light to kill the mold inside evaporator coil. Suggest to add surge protector for heatpump system. System is heating normal at this time