Garrett was courteous and extremely knowledgeable about his profession. He took measurements as well as photos of my unit, and came up with thorough proposals of different options for me to consider. A job well done!
Bo called before arriving, checked inside and out and quickly found the issue. He also let us know several ways to keep the system running at peak performance. Thanks so much for getting us comfortable again!!
We had Vu Tran come work on our unit doing basic up keep. When he was done with the service he let us know of a few things he noticed, and some courses of action. We never felt like he was up selling, or pressuring us. Great company, good price, and highly recommend!
Technician very professional, courteous and knowledgeable
Very courteous, knowledgeable, and professional.
Very courteous, professional, not pushy, friendly, found problem quickly
Replace Lennox manufacturer warranty evaporator coil. Pressure test and recharge system to manufacturer spec. Sign 2 CCI plan and complete 2 air conditioning maintenance. Change both 16x25x1 filter and flush drain system. Both system operating at this time.
Ac service Stone Mountain. Completed diagnostic. Found system frozen solid at evap coil. Can not diagnose properly at this time. Informed customer system needs to stay off overnight and we will return tomorrow to diagnose.
Tested system. Found refrigerant pressures to be normal. Changed dirty filter. Found compressor operating at high amperage. Condenser is from 1993. Due to age and condition of system, recommend upgrading condenser and evaporator coil to something more reliable and more efficient with a good warranty.
No cool main system, check and find blower wheel broken. Need to replace blower wheel. Need to check for availability and get back with customer for repair. Not yet collect for service call.
No cool. Check and find condenser fan motor not operating. Find burnt fan motor, missing disconnect breaker, compressor winding poor. Find inside unit very dirty, blower assembly dirty, gas line not up to code, flue pipe not up to code, and missing water protection. Furnace operating but intermittent missing fire for third burner. Customer need consultation visit. System off at this time.
A/c repair call for the main level, check and find broken control wire running to ac unit. Minor repair wire for customer, system operating at this time. Find a/c unit with a weak secondary motor controller and missing hard start kit and low on charge. Recharge system with 1 lbs of R22. Customers want to wait on repairing the system. System operating at this time.
A/c repair call. The tech was out yesterday and now the system not operating. Check and find a faulty contactor that was replaced yesterday. Replace with a new contactor and system operating at this time. Warranty service call, no charge to the customer
Sign 1 Comfort club membership. Complete 1 system a/c repair and preventative maintenance check. Change filter, check drain, and operations. Find a 10-year-old system in the crawlspace with a dirty duct system and condensation pump not operating properly and leaking water. Find an ac unit operating with worn pitted/burnt contactor. Replace the condensation pump and main electrical switch. System operating at this time.
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at email@example.com or call us at (770) 932-5012.
Arrived on site to preform a two system maintenance. Indoor; changed filters and cleared drain line. Checked electrical connections, amp draw and capacitance. Recommend adding secondary water safety switch to each unit. Outside made sure coils were clear, checked refrigerant pressures (found upstairs unit about 4lbs low. Charged to manufacture spec. Checked electrical connections, amp draw and capacitance. Both units are operating normally at this time. Charge upstairs unit to manufacture spec
Arrived on site to preform a two system maintenance. Inside: found upstairs unit had a blower capacitor reading low and an auxiliary drain pan switch, but no in-line switch. Checked all electrical connections and amp draw , cleared condensation drain line and changed filters. Outside; found both units with low reading capacitors. Recommend replacement and adding compressor assist kits to each unit due to age and to extend the life of the compressors. Cleaned condenser coils and checked refrigerant pressures. Checked all electrical connections and amp draw. Recommend installing surge protection to each unit to protect units from electrical surge. Both units operating at this time.
Complete 1 system a/c repair and preventative maintenance check. Check and find Lennox furnace flame sensor fail. Check and replace sensor. System operating at this time.