Completed one system furnace repair and preventative maintenance check. Check safety and operations. Change filter Aprilaire 810. Replace flame sensor, complete combustion calibration and reduce CO level to 25 ppm and improve efficiency to 81.7%. Pull and clean blower assembly. Suggest duct cleaning and suggest apco air purifier to improve air quality and help prevent molding. System operating at this time.