Found unit not kicking on due to bad voltage absorption system. Replaced voltage absorption system and signed customer up for 1 system maintenance plan. Voltage absorption system was under warranty so I credited $75 off the repair. Went ahead and did summer maintenance for customer. Left customer with replacement filter. Mechanical and electrical components in good shape. Found system low on 410a, recommend recharge. Recharged system to 10 degrees superheat. Chemically washed condenser coil. System operating at this time.