Reece was superb. Very professional, neat, timely and informative of tasks and issues he found
Found bad voltage absorption system and burnt wiring. Replaced voltage absorption system, replaced voltage distribution, added performance enhancement system, replaced voltage distribution system and renovated electrical wiring and terminations. Package comes with 1 year of maintenance and a 2 year electrical renovation warranty. Double checked refrigerant pressures for customer, they are in good shape. System cooling at this time.
No cool upstair system. Check and find air conditioner fail due to low charge. Check and find media coil badly rusted and leaking charge. Test and find compressor operating stress with high amp. System voltage absorption also weak. Suggest customer to upgrade system, customer want to wait. Customer want to repair system. Recharge system with sealer HJ8B. System operating at this time. Clean coil for customer due to coil dirty and causing high head pressure. If charge continues to leak out will need to replace cooling system. Test downstair system for customer, find system operating but have worn part due to age, high amp on compressor, weak voltage absorption and minor pitted on voltage distribution. Need to keep check on system. Suggest plan to help maintain system.
1 system ac tune up complete. Changed filter and added a nice citrus scent to it to bring a little extra freshness to the house. Found very rusty evap coil. Added chlorine tablets to evap coil drain pan. Found air escaping through hole where suction line and liquid line enter evap coil door, sealed it with caulk to stop airflow loss and increase airflow to house. Found high amp draw going to compressor and fan. Found worn voltage distribution system, recommend repair. Due to age and condition of system, recommend upgrading to a more reliable, more efficient system. If customer wants to make system last as long as possible, recommend repair on voltage distribution system and a performance enhancement kit to take a load off of the compressor. Found no surge protection, recommend adding on to protect unit from lightning strikes and power surges. Chemically washed gathers condenser coil and applied rust proof waxing. Refrigerant levels are good. System operating at this time.
2 system ac tune up complete. Changed upstairs filter. Found upstairs drain line clogged. We will come back to re route drain line for $325. Found main level blower motor controller running weak, recommend repair. Found blower wheel to be dirty, recommend cleaning. Upstairs condenser has a performance enhancement kit that isn't operating within manufacturer specs, recommend replacing performance enhancement system. Chemically washed condenser coils and applied rust proof waxing. systems operating at this time. Customer upgraded tune up to a 2 system maintenance plan.
Water leaking, check and find suction line insulation broken and condensation from suction line leak through ceiling. Add insulation for suction for customer and change 2 16x25x1 filter. Test and find upstair system low charge and fan motor making noise. Need to keep check on fan motor due to not reliable. Customer want to recharge system with sealer and performance enhancement HJ7C. System operating at this time. Suggest plan with Comfortcontrol inc to help maintain system.
2 System ac pm check complete. Changed filters. Added chlorine tablets in evap coil drain pans and condensate pump. Found main level low on 410a, recharged system. Checked mechanical and electrical components, all in good shape! Gave condenser coils a chemical wash and applied rust proof waxing. Systems operating normal at this time. Renew 2 system cci plan.
Found unit low on refrigerant completed job HJ2-B Quick fix and recharge Install internal sealers 90 day warranty Unit is cooling normal at this time Due to leak in unit and old refrigerant recommend replacing residential system.