Response from Comfort Control Heating & Air:
Victor, so glad we were able to provide you with 5-Star HVAC Service!
He was extremely helpful. Will definitely use this company again!!
Response from Comfort Control Heating & Air:
Thank you so much for taking the time to leave an excellent rating. We really appreciate your business.
The representative was very thorough and explained everything we needed to know. Very happy with the service.
Once again Comfort Control H/A out performed our expectations. The entire experience from the initial inspection and recommendations done by “Jeff” to the tear out and install performed by “Gavin” and “Ronnie” was painless and transparent. We were kept informed every step of the way.
I appreciate Jordan being honest on what he thought we should do! He seems quite knowledgeable!
Techs from North Atlanta Plumbing were very courteous and proficient. Was a pleasure to have them in our home
Extremely professional and helpful
Arrived within the time window. Was polite and efficient!
Not happy with my 5 week old system needing service already but liked the tech Alex. Had to change my Saturday schedule for the day to accommodate the service call
"Ricky" expediently, expertly, and cordially took care of us, performing our annual Spring AC maintenance [late...OUR FAULT!] yesterday, 07-08-21. Purchase and installation of this Amana Heating/AC system from Comfort Control -- way back in 2011 -- was one of the absolute best home improvement investments we've ever made.
Came out fast, professional and fixed the problem
The technician who visited my home was very thorough and professional, while explaining the issues with my hvac, and my options. Jordan did an excellent job.
Air Conditioner not working. Clogged drain lines. Cleared drains, air conditioner blowing cold air near mcginnis ferry road
AC Repair on 12 year old 4 ton Carrier system. Air conditioning not cooling properly, clean drain lines, diagnose and repair.
Air Conditioning Repair Suwanee. Air conditioner not blowing cold air, technician came out and determined bad capacitor. Replace capacitor HVAC system is operating smoothly near suwanee creek.
A/c diagnostic in Suwanee. Found indoor unit running, outdoor unit fan was running but not the compressor. Condenser has a bad secondary motor controller. Replaced capacitor system is cooling at this time. Blower wheel is clean, evaporator coil is clean, drain line is flushed.
Maintenance in 2 Goodman gas furnaces and AC. Both systems working at normal operations. Replaced downstairs condensate pump and hose. Recommended blower motor cleanings for both furnaces. Replaced 1 16x25x1 filter upstairs. Downstairs media filter needs to be replaced.
Ac service in Suwannee. Discovered system frozen and leaking refrigerant from evaporator coil. Due to age and condition replacement is HIGHLY recommended. Homeowner chose to refill refrigerant with ABSOLUTELY NO WARRANTY. Refilled refrigerant. System cooling temporary.
Ac service in Suwannee. Discovered old pvc Union gasket failing to seal properly. Removed Union and installed coupling with glue.
No cool Suwannee. Customer called about inadequate cooling. Found a leaking evaporator coil. Very dirty blower wheel. And weak capacitor. Due to leaking coil and cost of repairs I recommend a new system. Changed filter. Compressor is still good. Outdoor capacitor is within range. Pressures are low due to leak.
Replaced upstairs and downstairs evaporator coils
Maintenance Suwannee. Did a leak search on both evaporator coils. Did not find any leaks. Blower wheels are clean. Changed filters. Drain lines are clear. No cracks in the heat exchangers. Outdoor capacitors are both within range. Pressures on both systems are within range. Systems are cooling at this time.
Tune up Suwannee. Did a leak search on both evaporator coils. Did not find any leaks. Upstairs systems capacitor was weak. I changed the capacitor. Main level units capacitor is within range. Both blower wheels are clean. Filters are clean. Drain lines are clear. No cracks in either heat exchanger. Pressures on both systems are within range. One of the outdoor capacitors was weak. I changed that capacitor. The other capacitor was within range. Both systems are cooling at this time.
No cool in Suwanee. System is cooling at this time, customer said unit is icing up From time to time. Blower wheel is a little bit dusty, evaporator coil is rusty and clean but no leaks was found, also did fine the filter was pressed against blower housing, ( filter is inside furnace no filter rack ). Outdoor unit refrigerant pressures are good and all electrical components are working properly at this time.
Tune up Suwannee. Did a leak search on evaporator coil. Did not find any leaks. Changed filter. Indoor unit capacitor is very weak. Recommend replacing the capacitor. Drain line is clear. Blower wheel is clean. Outdoor capacitor is within range. Pressures are within range. System is cooling/heating at this time.
Ac service In Suwanee. Discovered furnace control board and blower motor failing intermittently, compressor over heated and weak outdoor capacitor. Cooled compressor down and system running at this time. Furnace is original to home and ac and evaporator coil is 11 years old. Due to age of system furnace replacement at minimum is HIGHLY recommended.
Ac service in Suwannee. Discovered melted wires in outdoor unit. Heavily corroded evaporator coil. Homeowner has chosen to replace ac and coil. Collected deposit and got system running until we replace.