Very knowledgeable in work.
They are professionals and did the job right the first time.
We were happy with Vu’s service
We had excellent experience with Vu Tran he was good in explaining the problem and quick in fixing it we were Very happy with service.
Garrett. Followed up on a service call that took place this morning to go over our options of replacing our heater. He was very pleasant, knowledgeable, understanding and helpful. We were able to collectively agree on our selection. I am very satisfied
Vu Tran demonstrated his knowledge and ability to evaluate our problem. We are very pleased with the service.
Complete heating maintenance in Suwannee. Did not change filter, check safety and operation. Find 5 year old Lennox furnace operating with minor ware in flame sensor and need to keep check. Find system have no inline water protection and not surge protection. Suggest safety for equipment and suggest air purifier to improve air quality and prevent molding. System operating at this time.
Three system cooling maintenance in suwannee. Arrived on site, changed filters and cleared drain lines, checked electrical connections, amp draw, and capacitance cleared outside coils and checked pressures found upstairs system without secondary water safty switch, recommend installing to protect electrical systems from water damage. Also recommend installing surge protection to each piece of equipment to protect electrical systems. Used the last of filtration media for PureAirX. Installed overflow switch and supplied customer with (1 box(4 uses)) PureAirX 16x25x1 media. All units are operating normally at this time.
No heat in Suwannee. Check and find new installed system not operating properly. Check and reset system setting. Test both zone and system operating at this time. Warranty service call. No charge to customer. Need to schedule for spring visit to check on system for cooling.
Furnace not heating in Suwanee, Georgia. Main level system. Found beckett tubing for condensate pump clogged causing water safety switch to trip. Unclogged tubing and system is heating at this time.
No heat in suwannee. Arrived on site, customer complaint of main level furnace not heating, found bad flame sensor. While in attic I also found that the upstairs system had a bad flame sensor and a warn ignitor. I replaced both ignitors and cleaned both flame sensors until we can get them in stock and come back to replace them (eta, mid following week). Got both systems operational again for the moment. Went through the check list, also found a weak capacitor on both systems. Should read 5mfd, out of spec reading (3.7mfd main level) and (3.5mfd upstairs) recommend replacing both. Both systems are without secondary water safty to protect unit
Complete 2 tune up special inspection in Suwannee. Check both 7 year old heating furnace. Check safety and operations. Did not change filter. Find both furnace in attic operating with in manufacturer spec. Suggest surge protection for both system, suggest air purifier system to improve air quality and prevent Bio growth.
Heating tune up in Suwanee, Georgia. Three systems. Changed filters. Tested mechanical and electrical components. Found upstairs system with dirty blower wheel. Recommend blower wheel pull and clean. Found upstairs gas line not up to code, it does not have a drip leg installed. Recommend installing drip leg on upstairs gas line to bring it up to code. Recommend installing overflow protection switches for downstairs and basement systems. Found basement main electrical switch with electrical pitting present, recommend repair. Systems are heating at this time.
Tune up suwanee. Completed tune up. Found blower and coil clean. Flame sensor and ignitor clean. Inducer motor is running high amps and could burn out. Capacitor for blower is very weak and needs to be replaced. Combustion is good. Air flow is good. Coil does have rust and corrosion on it indicating copper thinning. System has no secondary water safety to protect furnace from water damage or surge protection or indoor air quality.
Free consultation Suwanee Georgia 30024
Heat pump not heating in suwanee, Georgia. Down stairs system . Tested system and found , dirty blower wheel . Blower motor leaking oil. Found heat kit to be broken and bypassed. Found zone board with no dedicated transformer. Found evaporator coil very rusted , corroded, and actively leaking. Found mold inside system. Found dual capacitor to be weak (35/5). Found main electrical switch with electrical pitting present. Found evidence of system being grossly overcharged. Found compressor shutting itself off. Reduced refrigerant pressures to more appropriate levels and Compressor is still shutting itself off. Due to age and condition of system along with cost of repair, recommend upgrading system to a more reliable, more efficient system. Sending consultant out for a free consultation
Service call in Suwannee. Customer stated that master bedroom not comfortable due to lack of air flow. Check new carrier system. Adjust air flow to increase air flow to master bedroom. Reduce air flow to office. Complete combustion calibration service to increase temperature and efficiency of furnace. System operating with in manufacturer spec. Warranty service from install. Suggest zoning to improve control of comfort
Complete 3 heating tune up special inspection in Suwannee. Change filter, check safety and operations. Find both Lennox 9 year old furnace operating with under-fire furnace and not calibrated properly. Find downstairs furnace missing in-line water protection, flue pipe not code. Find basement Airhandler Trane 15 year operating with worn main electrical switch for heating kit. Find upstairs ac unit operating with weak condenser capacitor. Find main unit missing starter kit. Find basement heatpump missing starter kit. Find upstairs air distribution box have bio growth, suggest UV KIT to help kill and prevent molding. Sign 3 comfort control club care. Complete 3 heat maintenance. Install 2 PureAireX UV kit kill bio growth and prevent molding. Complete 2 Lennox combustion calibration service to improve temperature and efficiency. Replace basement Airhandler blower capacitor and main electrical switch. Install u starter kit for downstairs ac unit and basement heatpump unit. Replace upstai
Furnace maintenance in Suwanee, Georgia. Two systems. Changed upstairs pureairx filter pad. Tested mechanical and electrical components. Found upstairs furnace with weak blower capacitor (7.5uf). Recommend repair. Neither system has surge protection installed, recommend installing surge protection to protect equipment from power surges installed surge protection for furnaces and condensers. Replaced main level blower capacitor, part was under warranty, labor was not. Systems are heating at this time.
No heat in Suwannee. Discovered furnace with bad blower motor. Furnace is 28 years old and replacement is highly recommended over repair. Need to call on Monday to schedule consultation. Homeowner wants to shop around
Service call sunroom in Suwannee. Replace Lennox mini split head control system. Test and system operating at this time. Customer have $50 off coupon.