Been with them since 1991 and always happy with their service.
Will recommend any time
Once again, Ta Kim shows up ON TIME; proficiently HANDLES the inspection regimen in a fully RESPECTFUL manner.
Have been using Comfort Control for several years to service my HVAC. Always professional, on time, and good value for money spent.
Tech was on-time, efficient, and friendly.
Called today for a problem with my heater and the technician arrived within the hour! Fixed the problem quickly and efficiently. I was very impressed and would certainly recommend Comfort Control to everyone.
Very good service and very nice young man.
Installed 2 apco model SI u/v lighting systems. Both systems operating normal at this time
I complete heating pm check. The blower motor assembly is very dirty due to poor filter system. The control board is sending non-optimal signals and the blower motor is operating with high amps. The Evaporator coil is rusted and the supply plenum is made of fiberglass. The flame sensor is worn and showing non-optimal readings. The gas valve operational, but showing irregularities during operation. I recommend a UV light to improve indoor air quality for 550$. The system is need of a CO calibration. The system is operational at this time.
Replaced Inducer draft motor. Furnace is now heating properly. Homeowner was smelling gas. After the inducer motor was replaced the smell went away. Homeowner will call us if the gas smell returns.
Completed maintnenace on 2 systems. Upstairs flame sensor is border line, cleaned flame sensor but recommend new flame sensor and ignition system next year. Main floor unit is operating normal at this time. Air cleaner upstairs is good this visit and changed 1" filter on main floor unit. Replaced humidifier water panel, ran and tested humidifier.
Performed 2 System Maintenance. Homeowner wants to wait to re sign up for maintenance plan they are trying to sell the house. Filters will need to be changed upon next visit.
3 system heating tune up complete. Changed upstairs and basement filters. Tested mechanical and electrical components, all in good shape. Dusted out furnace cabinets and cleared barometric tubing. Systems heating normal at this time.
Found white and black mold in supply plenums. Installing Apco si's in each plenum. $1200. Installing on tuesday 21
MainFloor system is heating properly. I watched the furnace turn on the and run for 15mins. Tstat was off upon my arrival. Homeowners know to call if this occurs again.
Renew 2 cci plan and complete 2 heating pm check. Find both heating system operating with damage flame safety and minor worn ignition system. Find blower smc also baldly worn. Find both evaporator coil in attic dirty and rusted. Customer want to repair heating system for now. Renovate both heating system flame safety HM15A, replace both system blower SMC HN4A and upgrade upstairs tstat to aprilaire 8466. Change both filter. Both heating system operating at this time.
2 furnace pm check complete. Changed filters. Tested mechanical and electrical components, all in good shape. Systems heating normal at this time. Apco uv lights are 2 years old, the bulbs lose effectiveness after 2 years. Recommend changing.
Replace worn and noisy exhaust assembly for master bedroom system. Test and system operating at this time.
Smell gas on main system. Check and did not detect gas leak at this time. Check and find heating producing high level of exhaustion smell. Test and find heating system inducer assembly making noise and maybe not run at full speed from time to time and can cause heavy smell of exhaust. Need to replace inducer assembly before motor fail. System operating at this time.
Complete heating tune up. Change filter, check safety and operation. Find flue pipe not up to code, find heating system operating with little high CO level of 42 PPM but is it ok. Find minor ware on ignition and flame sensor and need to keep check. Overall, heating system operating normal. System in crawlspace and duct system not seal well, suggest duct sealing and APCO air purifier to improve air quality. Find evaporator coil baldy rusted and dirty.
Completed maintnenace on 2014 furnace. Customer not happy with humidifier we installed saying it is not keeping up the humidity level in the winter time. Need to schedule time to wire humidifier to come on with fan only to try and correct issue. Will have office call to schedule. Unit is heating great at this time.
1 furnace pm check complete. Changed 610 filter. Tested mechanical and electrical components, all in good shape. System is heating normal at this time. Recommend apco air purifier to keep evap coil clean and to kill bacteria, germs and viruses for improved air quality. Customer wants to reroute duct in living room, will do for $350 per Tom.