We have used Comfort Control for many years and all their technicians are very professional and courteous.
Customer reported that furnace was not heating. Turned system on and could not get system to duplicate the problem. Changed filter. Performed maintenance. System is heating at this time. Due to age of furnace, recommend upgrading it to a more reliable and efficient furnace.
Furnace maintenance in Suwanee, Georgia. One system. Changed filter. Tested mechanical and electrical components. Found blower capacitor to be weak (20uf), recommend repair. It is a zoned system with no bypass damper, recommend installing bypass damper to relieve static pressure when not all zones are operating. System is heating at this time
No heat for main system in Suwannee. Check and find Heating furnace fail due to fail control board. Need to replace gas furnace control board. Customer declined repair and will call home warranty for repair. System not operating at this time. Suggest to upgrade system due to age and cost of repair.
Heating maintenance suwanee. Completed maintenance on 2 systems. Upstairs is working good with no issues. Clean inside. Changed filter. System does not have secondary water safety device or properly ran gas pipe sediment trap to avoid debris getting into gas valve in furnace. Insulation in attic is also below beams in some part and needs insulation blown in to avoid heat loss in cooler weather. Downstairs system is old and has over heating inducer motor and very dirty blower wheel. System also has no water safety attached. Furnace downstairs needs to be replaced for better efficiency.
No heat in suwannee. Arrived on site, found inducer fan motor failed some time last night. Quoted to replace. Customer declined repair. System is not operational at this time.
Complete tune up special in Suwannee. Check and find 22 year old Armstrong gas furnace pressure port clogged. Clear port and system operating at this time. Find gas furnace operating with worn ignition, high temperature furnace and can over heat, rusted evaporator coil and bio growth on plenum, flue pipe not code and no water protection. Customer want to wait to upgrade system.
Call back in suwannee. Arrived on site, found float switch on condensation drain line tripped, reset switch and cleared drain line for maintenance customer. Tested unit. Unit is operating normally at this time.
No heat suwanee. Completed diagnostic found wires for gas valve loose. System turned on after tightening wires. Static pressure test indicates bypass damper not opening like it should causing furnace to trip on high limit. Inducer motor is failing. Evap coil is rusted all over. System has no back up water safety. System needs to be replaced due to cost of repair and efficiency of current system.
Furnace maintenance in Suwanee, Georgia. One system. Changed media filters and water panel. Set humidifier to 45 percent humidity. Tested static pressure and found it to be good. Tested mechanical and electrical components, all in good shape. Found mold inside supply plenum, recommend pureairx air purifier to kill mold, bacteria, germs and viruses for improved air quality. System has no surge protection, recommend installing surge protection to protect equipment from power surges. System is heating normal at this time. Thank you so much for your buisiness today! If you were happy with your service, please take the time to leave us a five star review on Google! Be sure to leave my name, Reece Wilson, in the review! And again, thank you for choosing Comfort Control for your heating and cooling needs!
Water leak call back in suwannee. Arrived on site, found screw in heat exchanger assembly loose causing water to flow into pan, made sure there was no damages to the system, tightened assembly and sealed. Tested system. Unit is operating normally at this time.
Heating maintenance suwanee. Completed maintenance on 2 systems. Main floor is heating good but has no water safety attached in case of clog. Also is older and not running very efficiently. Upstairs is running good with clean blower and coil. Has both forms of water safety. Changed both filters. Air flow is restricted upstairs due to multiple junctions being used. Suggest redoing ductwork to allow all rooms to come off of plenum to allow optimum airflow.
Two system heat maintenance in suwannee. Arrived on site, changed filters and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Recommended installing secondary water safty switch on upstairs system and surge protection to both systems. Both systems are operating normally at this time.
Furnace maintenance in Suwanee, Georgia. Two systems. Did not change filters, customer prefers to use more breathable filters and filters had recently been changed. Tested mechanical and electrical components, found no pressing concerns. Systems are 15 years old and may not last much longer though. Tested static pressure. Found downstairs system to have high static pressure , recommend installing additional 10â€ return and 8â€ supply for system. Recommend installing surge protection for furnaces to protect them from power surges. Systems are heating normal at this time.
Water leak in suwannee. Found no water leak, paint is pealing, but no wet spot in ceiling. No issues present at this time