We had Vu Tran as our technician. He knows the stuff very well and is very informative. No doubt an excellent service!
By provided excellent work & service.
Reese did a great job and was very personable
Our tech Jon was great. He was friendly, wore a mask and shoe covers, diagnosed the problem quickly and got it repaired for us.
Vu provides outstanding service. He is a very thorough technician. He found several issues that needed to be corrected in my new house. I can always depend on him to look out for the homeowner’s best interest. I have been a Comfort Control customer for over 20 years in my old house and look forward to having them service the units in my new home.
Great service, great technician very thorough. I have confidence that we will have a smooth running system.
This company is awesome. All staff are knowledgeable and nice. Prices are very reasonable! I really appreciated the cooler with cookies inside!! Kids love them!!
No cool basement system in Suwanee. Check and find 18 year old rheem system operating with empty R22 and worn parts due to age. Find system leaking at evaporator coil in basement. Customer need consultation visit. System off at this time and only fan operating.
Heating furnace maintenance in Suwanee. Tested operation on 2 furnaces. Discovered upstairs furnace flame safety with weak readings. All other components tested within normal manufacturing spec. Changed humidifier pad on downstairs system and turned on humidifier. Replaced upstairs flame safety
Water leak for main level air conditioning system in Suwanee. Check and find 16 year old weather king system operating with stress blower motor and Nordyne air conditioner unit little low on charge due to small leak at evaporator coil. System operating at this time. Evaporator coil not freezing up at the moment. System operating at the moment. Need to keep check on furnace control board and blower motor.
HVAC heating issue in Suwanee Georgia . Looked over heating system . â€¢Got the pilot lit for the furnace in the basement . Going to complete a tune up for the basement furnace. Checking the performance and safety for this heating system . â€¢Found the inducer has high amps . Due to age of the equipment. â€¢ High limit switch was tripping on todayâ€™s visit and has burn marks on the switch. High limit switch is going bad . Would suggest replacing that part . â€¢Flue pipe is single wall would highly recommend being double wall due to the way the furnace combust . â€¢System has no form of water safety to prevent water damage in the basement would highly recommend. â€¢Would highly recommend upgrading the HVAC equipment due to age and conditions/ lack of efficiency of the old technology . If not interested in upgrading at this time would suggest putting this machine on a maintenance program . â€¢Indoor coil is very rusty and will eventually lead to the R22 leaks . Set up a
â€¢Completed two system heating maintenance in Suwanee Georgia . Checked safety and performance. Checked heating elements and heating integrity. Today is the prepaid visit for the maintenance. â€¢Main floor furnace . Found the flame reader is getting weak took pictures. Would highly recommend replacing that electrical part to prevent future issues. $159.80 part is under warranty but the labor and time is not . Family is going with replacing the flame reader today . Replaced electrical part and working at speck levels . â€¢Upstairs furnace . Replaced restricted air filter with a new April air 610 filter . $55 . System is heating at this time :) . â€¢Also sending the family a proposal on installing UV air purification systems to the air plenums on the HVAC equipment. â€¢Total today $214.80
Free consultation in Suwanee for new hvac system
Complete 3 heating furnace tune up special in Suwanee. Change all 3 filter, check safety and operations. Find both upstairs and main level Armstrong gas furnace 19 year old operating with weak flame sensor, worn ignition, weak blower capacitor, rusted Evaporator coil and missing water safety. Find upstairs furnace power switch overheated and damage and control board resistor overheating. Find downstairs furnace overheating and high supply temperature and flue pipe operating at 420 degree. Blower assembly very dirty. Find basement Airhandler system operating with rusted evaporator coil and bio growth. Due to system age and worn conditions, suggest to upgrade system.
Complete 2 heating maintenance pm check in Suwanee. Change filter, check safety and operations. Find upstairs air conditioner unit was not operating due to breaker was set on off, turn on breaker and system operating. Find 6 year old carrier furnace operating but oversized for house, missing return box. Find downstairs heating furnace operating with rusted heat exchanger, worn motor, gas valve and high CO level. Due to system age and poor conditions, suggest to upgrade system. Customer need consultation visit
Water leak suwanee. Completed diagnostic. Drain line was clogged. Float switch did not kill system. Cleared drain line. Repositioned float switch and tested. Float switch works. Tested drain. Water flowing properly. No water accumulating in return box. Freon levels are good. System cooling at this time.
Replace Lennox 4 Ton evaporator coil in attic with 5 Ton Lennox evaporator and replace metering device for system. Pressure and recharge system to manufacturer spec. Replace furnace control board. System operating at this time. Need to schedule in November to do heating maintenance.
No cool main level Goodman 15 year old air conditioning system in Suwanee. Sign 3 CCI plan and complete 3 heating maintenance. Change 2 16x25x1 filter, check drain and clean 3 condenser coil. Find both heating system operating with weak flame sensor, worn ignition and weak blower capacitor. Find both Evaporator coil In attic leaking and baldy rusted. Both system missing in-line water protection. Find both condenser with low charge and burnt damage capacitor and line wire. Due to system age and conditions, suggest to upgrade equipment. Customer want to repair system for now. Recharge both system with R22, replace main level unit capacitor and repair wires. Replace flame for upstairs system in attic. All 3 system operating at this time.
1 Ac coil complete in Suwannee. thank you for your business! Mark and Gavin!
5 - 8â€ 3 - 6â€ 2 - 4â€ 8â€ in each bed room and hallway. 6â€ in master bath and by master bed. 4â€ in master closet and hall bathroom Add 8â€ return in bonus up high. Add 8â€supply in bonus room on opposite side close to window wall.
No cool master bathroom system in Suwanee. Check and Find system short cycling due to compressor not starting properly and shut off on safety. Install hard start kit and sureswitch main electrical kit with time delay to prevent system coming on and off. System operating at this time.
No cool in Suwannee, arrived on site, found 1/3 of the plenum for main level system had torn away from unit creating a massive air leak. supported front of plenum and Re-sealed. No other issues present at this time. Signed customer up for a 2 system maintenance to start in fall