Ta went to work fast, gave me options and fixed the problem!
Excellent overall experience in getting diagnosis of AC not working issue. From beginning to end, it was first class. Reece was great with thoughtful, detailed recommendations of what is necessary to fix the problem. Highly recommend.
I highly recommend. Very prompt and professional. Answers questions and gives good advice.
Tea is consistently excellent with his advice and ability at maintaining our modern system.
3 system ac prepaid pm. Replaced filters, cleared drain and clean clogged condenser coil. Found upstair and downstair system with weak hard start and upstair has bad capacitor. Downstair low on freon. Owner just wants to add freon for now. Added 2 lbsnof r22 to downstair system.
Freon is low and secondary motor controller is weak and will fail.
Installation of secondary drain pan for the attic unit of the leasing office. *Note pricing listed is an estimate and can be subject to change based on the variables of the location and size of the unit. Any pricing changes will be pre-approved by both parties before any work is performed. For any additional questions please contact us at email@example.com or call us at (770) 932-5012. Airhandler is too old to move. Recommended upgrading Airhandler. Condenser was just replaced a few months ago. Quoted to replace the Airhandler.
No cool. Check and downstairs ac unit fail due to bad Tstat and faulty compressor capacitor. Replace capacitor and repair Tstat with Aprilaire 8467. System operating at this time. Find upstairs system starter weak and low charge. Install compressor hard start kit and recharge system. Test and find system operating but have high head pressure but operating at this time. Clean both outdoor unit for customer Due to coil very dirty.
Warranty leak in evaporator coil.
Found bad capacitor at the blower and relay for the blower bad. Wired direct to get cooling. Recommend upgrading due to age and condition. Quoted new complete systems.
Replaced bad blower motor controller on basement system, added 1 lb of Freon ton the main floor system, added 1 lb Freon to the up stairs system and repairs the insulation inside the coil box on the upstairs system. Performed 3 system a/c repair and preventative maintenance checks.
Completed a/c repair and preventative maintenance check. Replaced filters. Drains are clear. Amps and pressures are good. Tightened electrical connections. Chemical washed condenser coils. Systems are cooling well at this time.
3 system a/c repair and tune_up complete. Found weak blower motor controller in the upstairs system (7.5 uf). Found weak blower motor controller in basement system (5 uf). Found main level system very low on r22 causing system to freeze up. Found basement and upstairs systems both slightly low on r22. R22 is being phased out by the EPA in 2020. Chemically washed condenser coils. Recharged the main level system with 4 lbs r22, recharged upstairs and basement systems with 1 lb r22 each. Added leak seal to all systems (not guaranteed). Replaced upstairs and basement blower motor controllers. Systems are cooling at this time. Customer upgraded tune-up to a Comfort Club Membership plan.
Maintenance check is done on the system. Found the system leaking while doing the check. Quoted new condenser and coil.
Replaced main level evaporater coil under full warranty. Flushed with nitrogen, pulled vacuum to 300 microns and charged system to 6 degrees subcooling per manufacturer specifications. System is cooling at this time.
One system a/c repair and tune up complete. Changed filter. Found water in drain pan caused by improperly constructed drain line. Did a quick reconstruction for drain line to drain properly. Found evaporator coil to be rusty and corroded. Did a leak search and found a leak in the evaporator coil. Refrigerant pressures are okay at this time but evaporator coil is actively leaking. There is no water safety on system to shut it off as a safety in the event of water in the drain pan. Voltage absorption system is running weak. Due to age and condition of system, recommend upgrading system to a more reliable, more efficient system. System is cooling at this time. Added leak sealer to system (not guaranteed) and replaced voltage absorption system
Found leak in evaporater coil. Will return to replace coil under full warranty